very polite, jason is very thorough in what he is doing, very satisfied
Personal. Professional service
Dave did a nice job!
Response from Fire Pros, LLC:
Thank you Chris for the 4 star review.
Portable Extinguishers and Kitchen Suppression Inspection
Completed puff test and relocated pull station per fire Marshall request.
Wet South West office closet: Remove and replace the tamper switch on the PIV that is broken. NOTE: If additional wiring or connections are needed, the customer will need to contact the alarm vendor for this.
DD RTU-1: DD’s ADDRESS 30 and 31 IN 3RD FLOOR HATCH IS STILL NOT WORKING. STILL NEEDS TO BE REPLACED. POTTER PAD 100. (2) DUCT DETECTORS TOTAL NEEDING REPLACEMENT. - This deficiency was stated at last year's inspection and also 2021.
Annual Fire Alarm Inspection Potter panel- 43 SD, 1 HD, 6 DD, 11 MP's, 1 flow, 2 TS, 39 HS's, 14 Strobes, 72 low Freq. HS's
Alarm Systems Inspection
Annual Fire Alarm Inspection- Fire Alarm Panel- (1) (Mircom - Series 1000- Main panel in the basement by riser) (41) initiating devices - all common areas (30) indicating devices - all common areas (2) sets of door magnets - all common areas (1) booster on the second floor (1) annunciator (main entrance)