My only complaint is that it took longer than expected to get the proper smoke head in stock so the tech could come to complete the install. The techs are always do a great job trouble shooting my system & getting it corrected.
Replaced Smoke Detectors In Rooms 503 and 504 ***All systems Normal and Reset ***
Arrived on-site and found the system showing 36 Troubles (36 Devices were missing in the 400 Hallway) Found after investigation that the 400 hundred hall Laundry Room was Remodeled and the splice box in the room was painted with all the wiring exposed. Found Loose wiring connections and Re-Connected. Cleared all Troubles and had to replace 2 smokes that were in CAL TBL in Rooms 408 and 410 Bedrooms. Reset System and Reset all Fire Doors. Upon leaving system reflected 2 more Additional smokes that went into CAL TBL in Rooms 503 and 504. Informed customer and got Pre-Approval for replacement of those smokes which will have to be ordered.
PORTABLE FIRE EXTINGUISHERS: (12) New 5#ABC Fire Extinguishers installed throughout the (6) Suites of the Strip Mall (2 in each - front and back). Service includes all Labor and Materials to complete. INCLUSIONS: > Installation of the Fire Extinguishers - including the necessary Mounting Brackets. > Installation of location Signage, where necessary
Replaced Smoke Detector in Room 814 BDRM ***All systems normal and reset ***
Corrected Deficiencies from inspection and Replaced 2-Smoke Detectors that requires replacement ***All systems Normal and Reset ***
Alarm Systems Repair
Replaced smoke detector in room 603 B BED RM
Replaced smoke in rm 614 A Hall and reset system ***All systems normal and reset ***
Alarm Systems Service Call
Replaced smoke and H/S in 600 Hall west Storage room and tested system ***All systems normal and reset ***