Nice work! Professional and personable at same time!
Alex was pleasant to work with. The only issue was that the work window scheduled was not observed.
keep up the good work your team is awesome.
the two guys that came to Medilodge of Farmington were very helpful knowledgeable and good at what they were doing Mr. Jones had a trainee with him he was Mr. Green and you couldn't even tell that he was a trainee because he new his stuff.
TERRENCE WAS VERY EFFICIENT AND PROFESSIONAL
10/13/23 Sent email regarding inspection Sprinkler and Antifreeze Loop Inspection Annual Fire Sprinkler Inspection (1 Wet Sytem) Annual Antifreeze Loop Inspection (1)
10/6/23 Confirmed with Bill for 10/9/23 at 11:30 DH 9/26/23 Sent email regarding inspection Bill said not today, he can't get there to unlock the door. DH 9/11 Unable to get into the building 9/8/23MV Bill confirmed Sprinkler Inspection Annual Sprinkler Inspection Deficiency: Sprinkler system will need control valve, sign, as well as antifreeze sign for identification
7/13/23 Sent email regarding inspection DH Sprinkler Inspection Quarterly Fire Sprinkler Inspection (1 Wet System)
Sprinkler Service Call Service call from Art N. having flow switch issues and alarm keeps going off.
4/4/23 confirmed by Art N. via email for 4/5/23 at 10:00AMish DH / Sent email regarding inspection DH Sprinkler Inspection Quarterly Fire Sprinkler Inspection (1 Wet System)
3/3/23 Sent email regarding the inspection DH Sprinkler Inspection Annual Sprinkler System Inspection
1/5/22 Confirmed with Gordy with Art for 1/13/22 at 10:00 DH Sprinkler Inspection Quarterly Fire Sprinkler Inspection (1 Wet System)
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected/serviced the fire sprinkler system at your establishment in accordance with NFPA guidelines. While inspecting/servicing your fire sprinkler system, it was determined to be "Non-Compliant". The attached proposal summarizes the non-compliance issues that were found during the inspection/service and the costs and actions needed to correct them. Fire Systems of Michigan strongly recommends that your sprinkler system is repaired so that it will become compliant. If obstruction is present, this can render the sprinkler system to not properly operate in the case of a fire. NFPA 25 (188.8.131.52) Inspection of the internal condition of piping shall be conducted at a minimum of every 5 years for the purpose of inspecting for the precedence of foreign organic and inorganic material. This is a safety hazard and may contribute to damage or injury to your property and individuals in the event of a fire. Please cont
Portable Extinguishers Inspection