all that was done was the fire department hook up in the back of the building was check
He was extremely friendly and knowledgeable. We love having him out to our business, he's always helped us in our Westland location. Equipment was the problem with repeated service calls, tech was awesome.
Trouble Shot System, Removed Quick Disconnect wiring clips and re-wired all panel wiring to mother board screw terminals. Checked batteries and programed opening and closing reports. And tested system. Could not Re-create any Actual Alarm Conditions. ***All Systems Normal and Reset ***
A Hall checksit was loose causing system not able to arm/Disarm Re-Tightened Checksit and Tested*** All Systems Normal and Reset ***
Trouble Shot System (System Reflected Horn South open ckt) after investigation found blown 3A 250 volt Glass fuse on simplex mother board. Replaced Fuse and Reset system. ***All systems Normal and Reset ***
Completed Annual nurse call inspection for 2018
Completed Annual Fire Alarm inspection for 2018
Completed Annual extinguisher and emergency light Inspections for 2018