Robert Willis is awesome very professional and he explains things very well. Great guy
I was very impressed with the professionalism and the service that I received. They worked hard to finish the inspection so I could get ready to open. I highly recommend them
Your service tech, who's name I am forgetting was excellent. We had an internal problem getting the system set into test and your tech was pleasant and accommodating with our delay.
3/17 Jim requested and confirmed appt. Call him when you're on the way: 734-383-3328. Either he or a custodian will meet you here km 3/9 LM for Lisa on her vm km 2/26/21 Called and left a VM for Lisa SM 1/7/21 - LM on VM mh Kitchen Suppression Inspection Semi-annual Kitchen System Inspection
3/3/21 confirmed with Gerrad for 3/10/21 sM 1/8 NA at 8:00 am km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection
1/4 Service requested and confirmed by Stephanie, via phone message. Emailed confirmation with alarm info. km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection 4 extinguishers Semiannual Kitchen System Inspection Deficiency: Number of Systems failed : 2 Deficiency: Number of Extinguishers Left at Job: 3 Deficiency: Chain oven unprotected. Deficiency: 9 Gallon Ansul System and 3 Gallon Ansul System out of hydro date. Deficiency: 1- K-Class fire extinguisher 1- 5# abc fire extinguisher Due for hydro test. 1- 10# abc fire extinguisher due for 6yr maintenance.