Robert Willis is awesome very professional and he explains things very well. Great guy
I was very impressed with the professionalism and the service that I received. They worked hard to finish the inspection so I could get ready to open. I highly recommend them
Your service tech, who's name I am forgetting was excellent. We had an internal problem getting the system set into test and your tech was pleasant and accommodating with our delay.
1/4 Service requested and confirmed by Stephanie, via phone message. Emailed confirmation with alarm info. km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection 4 extinguishers Semiannual Kitchen System Inspection Deficiency: Number of Systems failed : 2 Deficiency: Number of Extinguishers Left at Job: 3 Deficiency: Chain oven unprotected. Deficiency: 9 Gallon Ansul System and 3 Gallon Ansul System out of hydro date. Deficiency: 1- K-Class fire extinguisher 1- 5# abc fire extinguisher Due for hydro test. 1- 10# abc fire extinguisher due for 6yr maintenance.
10/14 Confirmed with Aaron. He'll be on site for you. km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Ansul R102-S1.5 (1)360 link (3)Nozzles