Very professional! We appreciate Matt's help with making sure our office is up to code.
Everyone has always taken the time to answer my questions.
Rhonda called - comm2 error that wont clear on the panel 231-928-1255- system sent a comm fail tues/wed and did not test Thursday AM- reprogram test time for in the 7AM hour-
Portable Extinguishers Inspection
Add/delete arming codes as requested by Maddie list is attached.
Portable Extinguishers and Emergency / Exit Lights Inspection
Joe approved service work on site
EMCOR Paperwork Attached Annual Fire Alarm Inspection
Deficiency: 18 smoke alarms are out of date code and should be replaced Deficiency for HD MECHANICAL ROOM: Mechanical room 120 V heat detector is out of date and should be replaced