Great to work with, very professional.
Corey showed up on time and was well prepared for any work we needed, which included upgrading our signage/extinguishers without having to come back. He was pleasant and professional and able to give price quotes ahead of time. Corey also provided insight as to what we may need to upgrade in the future to keep us the safest. He was attentive to the needs of our business and hope to see him for the next inspection!
On time, company communicated every step of the way!
Very smooth and helpful.
We were a couple weeks overdue and played some phone tag trying to lock down a day/time, but overall service was good and pretty convenient. No complaints.
Alarm Systems Inspection
Inspected 4 industrial systems
Kitchen Suppression and Portable Extinguishers Inspection
Per Craig they have fire extinguishers that need to be picked up for service Return (1) extinguisher pulled for service 2/3/2020
Inspected 7 fire extinguishers and 12 lights. Installed 2 new 10# abc fire extinguishers. Exchanged (1) 10# abc fire extinguisher for 6 year and replaced 2 batteries. Installed (2) fe signs and mounted 1 extinguisher
Suggested: There is no notification in the second-floor office area. This is a 50’x 80’room. Employees said they only heard alarm because they knew I was testing it. Bell circuit one is available on the FACP. Adding 1 Horn strobe would take 30 foot of wire go through two short drop ceiling one in panel room one in conference room and horn strobe could be mounted on outside of conference room wall. 30’ 14/2 WIRE 1 GENTEX GEC3 1 CUT IN BOX 2 HOURS LABOR
Inspected 3 fire extinguishers, 7 lights and 1 kitchen suppression system. Replaced 2 metal caps, (1) 2H nozzle, 8 links and (2) batteries. Approved by manager on site Ken kelling
Portable Extinguishers Inspection