Great to work with, very professional.
Corey showed up on time and was well prepared for any work we needed, which included upgrading our signage/extinguishers without having to come back. He was pleasant and professional and able to give price quotes ahead of time. Corey also provided insight as to what we may need to upgrade in the future to keep us the safest. He was attentive to the needs of our business and hope to see him for the next inspection!
On time, company communicated every step of the way!
Very smooth and helpful.
We were a couple weeks overdue and played some phone tag trying to lock down a day/time, but overall service was good and pretty convenient. No complaints.
Completed install of kitchen suppression system
Portable Extinguishers Inspection
Emergency / Exit Lights and Portable Extinguishers Inspection
Commercial fire ppwk-you have ONE HOUR- call for more time if needed or for approval for parts. Scope of work: Battery problem with our panel
Deficiency: Unable to do the conversion at this time. This is an ADT focus we cannot reprogram. This will need a toll guard TG7 to complete monitoring conversion. Send quote with line items to Commercial Fire.
Annual Fire Alarm Inspection
Suggested for FACP OFFICE RISER ROOM: telephone lines not working properly to facp. Line 2 is completely dead line one works intermittently. Customer to call phone company. Fire Pros to quote cellular communication for facp to Criticom Deficiency for Dry Art studio, closet: Chris would still like a quote for cellular communication inside of the FACP so phone line troubles with AT&T can stop whenever they are working on phone lines.
Annual Fire Extinguisher Inspection (4 FE) Portable Extinguishers Inspection
Comm fire ppwk Complete fire alarm conversion then the annual fire alarm inspection. complete all required paperwork.
Inspected 19 fire extinguishers
Perform a 5-year internal assessment of system piping that is due. If an obstruction is present, this can render the sprinkler system not properly operate in the case of a fire. Tech will need to perform testing in the main entrance. They will not be able to access any other areas of the building due to the walkway width and height of the ceiling. NFPA 25 (220.127.116.11) An assessment of the internal condition of piping shall be conducted at a minimum of every 5 years or in accordance with 18.104.22.168 to inspect for the presence of foreign organic and inorganic material. Perform a 5-year internal inspection of the system check valve of both systems. NFPA 25 (22.214.171.124) Alarm valves and their associated strainers, filters, and restrictions orifices shall be inspected internally every 5 years unless tests indicate a greater frequency is necessary. Perform a 5-year internal inspection of the Fire Department Connection (FDC) check valve. NFPA 25 (126.96.36.199) Check valves shall be inspected in