Annual Fire Alarm Inspection (95 Devices) (Simplex 4005)
This quote is for the City of Grand Ledge Public Services Department. To have Fire Pros get the equipment needed to monitor your Fire Alarm cellular. Also the technician will set up the equipment and test with monitoring station.
There is a new ground fault on output four of booster panel..This output goes towards shower area . Quote is for troubleshooting ground on wire .
Deficiency: ground on wire- need more hours to track and keys to IT closet. Deficiency: There is a new ground fault on output four of booster panel..This output goes towards shower area Deficiency: Room F horn strobe was causing ground fault on output three. Bypass horn strobe in room F. Need to quote and replace with system sensor P2RL
Deficiency for Main Basement: Pyrochem pcl-460 4.6gallon tank dated 2007. Due for hydro test and recharge Deficiency: Pyrochem pcl-460 4.6gallon tank dated 2007. Due for hydro test and recharge Pyrochem pcl-460 4.6gallon tank dated 2007. Due for NFPA 17A required hydro test and recharge - repair Kitchen Suppression Repair
Replaced horn strobe in shower number nine and tested. Tracked different open wires on loop going towards restaurant. Found a booster panel hidden above the ceiling that is bad battery 8 V and charging circuit is shot and needs to be replaced. Commercial fire would like a quote for replacement of booster panel. Found open in attached wires at booster and in loop. (Possibly from restaurant). Only 3 outputs of 4 are being used on booster. After booster is replaced can track wires through restaurant ALL WIRES IN CONDUIT. I saw exposed open wires at box where a horn strobe should have been (pics in attachments) - repair
- 6 horn strobes in restaurant area did not operate during inspection, restaurant is permanently closed. a combo of P2R and P2RL. -QUOTE TO TROUBLESHOOT ONLY - strobe in shower 9 did not operate during inspection - QUOTE TO REPLACE
Inoperable Deficiency: M 22 module for duct Detector by showers was in trouble upon arrival does not work, this trouble was reported last year Deficiency: to troubles on panel upon arrival in 22 and M16, manager stated both troubles have been there forever Inoperable Deficiency: strobe in shower 9 did not operate during inspection Inoperable Deficiency: 6 horn strobes in restaurant area did not operate during inspection, restaurant is permanently closed. a combo of P2R and P2RL.
Annual Exit & Emergency Lighting Inspection (33 Units) Annual Fire Extinguisher Inspection (29 FE's) Semi-annual Kitchen Suppression System Inspection (PCL 4.6 gal)
medical pull cord was pulled in room 413 but room 412 is what shows tripped
Annual Alarm inspection (129 devices) (Potter P 300) (per note in acct - 2 techs needed. not sure if that's how its priced)