Inoperable Deficiency: M 22 module for duct Detector by showers was in trouble upon arrival does not work, this trouble was reported last year Deficiency: to troubles on panel upon arrival in 22 and M16, manager stated both troubles have been there forever Inoperable Deficiency: strobe in shower 9 did not operate during inspection Inoperable Deficiency: 6 horn strobes in restaurant area did not operate during inspection, restaurant is permanently closed. a combo of P2R and P2RL.
Annual Exit & Emergency Lighting Inspection (33 Units) Annual Fire Extinguisher Inspection (29 FE's) Semi-annual Kitchen Suppression System Inspection (PCL 4.6 gal)
medical pull cord was pulled in room 413 but room 412 is what shows tripped
Annual Alarm inspection (129 devices) (Potter P 300) (per note in acct - 2 techs needed. not sure if that's how its priced)
Check panel unable to communicate. Call Shane for Details
Alarm Systems Inspection
I temporarily adjusted the tamoer switch to restore system trouble.
Emergency / Exit Lights, Kitchen Suppression, and Portable Extinguishers Inspection
Emergency / Exit Lights, Portable Extinguishers, Kitchen Suppression, and Alarm Systems Inspection