Replaced horn strobe in shower number nine and tested. Tracked different open wires on loop going towards restaurant. Found a booster panel hidden above the ceiling that is bad battery 8 V and charging circuit is shot and needs to be replaced. Commercial fire would like a quote for replacement of booster panel. Found open in attached wires at booster and in loop. (Possibly from restaurant). Only 3 outputs of 4 are being used on booster. After booster is replaced can track wires through restaurant ALL WIRES IN CONDUIT. I saw exposed open wires at box where a horn strobe should have been (pics in attachments) - repair
- 6 horn strobes in restaurant area did not operate during inspection, restaurant is permanently closed. a combo of P2R and P2RL. -QUOTE TO TROUBLESHOOT ONLY - strobe in shower 9 did not operate during inspection - QUOTE TO REPLACE
Inoperable Deficiency: M 22 module for duct Detector by showers was in trouble upon arrival does not work, this trouble was reported last year Deficiency: to troubles on panel upon arrival in 22 and M16, manager stated both troubles have been there forever Inoperable Deficiency: strobe in shower 9 did not operate during inspection Inoperable Deficiency: 6 horn strobes in restaurant area did not operate during inspection, restaurant is permanently closed. a combo of P2R and P2RL.
Annual Exit & Emergency Lighting Inspection (33 Units) Annual Fire Extinguisher Inspection (29 FE's) Semi-annual Kitchen Suppression System Inspection (PCL 4.6 gal)
medical pull cord was pulled in room 413 but room 412 is what shows tripped
Annual Alarm inspection (129 devices) (Potter P 300) (per note in acct - 2 techs needed. not sure if that's how its priced)
Check panel unable to communicate. Call Shane for Details
Alarm Systems Inspection
I temporarily adjusted the tamoer switch to restore system trouble.
Emergency / Exit Lights, Kitchen Suppression, and Portable Extinguishers Inspection
Emergency / Exit Lights, Portable Extinguishers, Kitchen Suppression, and Alarm Systems Inspection