Site had a fire in lobby area. Replace wiring/detectors in lobby (2) and laundry room (1). (Pt 14) and Lobby Smoke Detector 2 (Pt 15). These two points will remain in trouble until lobby renovation is complete. New Lobby will have drop tile ceiling, pull cord was left at ceiling height to existing lobby pull station for SLC loop wiring. Quote to: Replace 2 Lobby Smoke Detectors and Replace Laundry Smoke Detector . Complete System Testing following renovation/remediation Cellular Monitoring - separate from repair/replacement Copy any quotes/paperwork to email@example.com This quote is for FSM to provide 3 new fire alarm devices for the lobby / laundry areas. Installation, Permits, Programming and Testing included.
CP UTILITY ROOM: FACP IS NOT FUNCTIONING AT ALL AND NEEDS TO BE REPLACED. PANEL IS CONVENTIONAL AND IS USING 2 NACS AND 4 ZONES. CAN BE REPLACED WITH A FIRELITE MS-4. - repair This quote is for the replacement of the non functioning fire alarm system. This is only a panel swap replacement . Test system when complete. Any additional work needed will need to be quoted.
Annual Alarm Inspection (22 devices)
Annual Fire Alarm Inspection (18 devices) (Silent Knight 5207)
Annual Fire Alarm Inspection (30 devices) (Silent Knight 5207)
Annual Fire Alarm Inspection (24 devices) (Firelite MS-2)
Annual Fire Alarm Inspection (29 devices) (Notifier SFP 2404)
Annual Fire Alarm Inspection (15 devices) (Firelite MS 4424)
Annual Fire Alarm Inspection (28 devices) (National Time 902-SG)