Great service, very thorough
I appreciate Camp's professionalism and customer service. Highly recommend Fire Pros to service your needs.
Completed annual extinguisher and emergency exit lighting inspections for 2019
Returned 3- 10 Lb CLEAN GUARD Extinguishers (2- Onclave) (1-Imagery Server Rm) After Being Serviced and Removed 3 5lb CO2 Loaners
Replaced FACP BATTERIES THAT FAILED LOAD TEST FROM RECENT INSPECTION 2-12 volt 75 ah batteries *** All Systems Normal and Reset ***
Completed Annual Fire Alarm Inspection
Completed annual Fire Alarm inspection for 2019
Replaced Monitor Module in Meat Cutting Room (Device M3-32 MEAT CUTTING RM HD PROBE) ***All Systems Normal and Reset ***
Annual fire alarm system inspection.
Semi-Annual Inspections of the Clean Agent Fire Suppression Systems located in the 1408 building (2 Systems - Janus & Kidde)
Completed Annual Extinguisher and Emergency/Exit Light Inspections for 2019 On buildings 1408,1409,1425
Completed Repairs on Extinguishers in buildings 1408 and 1425
Completed Annual Fire Alarm and Extinguisher Inspections in Buildings 1408, and 1409 ***All Systems normal and reset***
Systems Normal upon Arrival Investigated Troubles Found M3-32-Meat Cooler Heat Detector was going in and out of trouble Due excessive condensation and EOL resistor being broken off causing trouble. Replaced EOL 47K ohm resistor and Reset system. Also Replaced water damaged Horn/Strobes in meat cutting and meat wrapping rooms. ***All systems Normal and Reset at this time ***
Semi-annual FM 200 suppression system inspections.