Great service, very thorough
I appreciate Camp's professionalism and customer service. Highly recommend Fire Pros to service your needs.
REPLACED MEAT CUTTING ROOM WEST HEAT DETECTOR PROBE MODULE AND WEATHER PROOFED BOX WIRING CONNECTIONS ABOVE AND BELOW COOLER AND RESET SYSTEM. ***All Systems Normal and Reset ***
Replaced batteries in lights in building 1409 Rms 116 and 142 and tested ***All Systems Normal and Reset ***
Alarm Systems Repair
Semi-Annual Inspections of the Clean Agent Fire Suppression Systems located in the 1408 building (2 Systems - Janus & Kidde)
Arrived On-Site Found System In Alarm and Trouble. Found meat cutting room module in trouble (Missing) upon arrival, and oven in Deli was shut down, 1st Trouble shot Oven being shut Down. Found that the dry riser was dumped causing the alarm and tripped the shunt trip for the power. Found that a sprinkler head on dock was leaking air and eventually dumped the system. Shut down and drained System and Reset Alarm. Oven power was restored. 2nd Trouble Shot Meat Cutting Room Missing device, Found Heat Detector probe module was wet due to condensation. Have to quote labor and part replacement. System will remain in trouble until module is replaced. System Alarms have been restored only Trouble remains. Assisted sprinkler Technician to replace head and reset dry system.
Completed annual extinguisher and emergency exit lighting inspections for 2019
Returned 3- 10 Lb CLEAN GUARD Extinguishers (2- Onclave) (1-Imagery Server Rm) After Being Serviced and Removed 3 5lb CO2 Loaners
Replaced FACP BATTERIES THAT FAILED LOAD TEST FROM RECENT INSPECTION 2-12 volt 75 ah batteries *** All Systems Normal and Reset ***
Completed Annual Fire Alarm Inspection