Great service, very thorough
I appreciate Camp's professionalism and customer service. Highly recommend Fire Pros to service your needs.
Completed Annual Fire Alarm and Extinguisher Inspections in Buildings 1408, and 1409 ***All Systems normal and reset***
Systems Normal upon Arrival Investigated Troubles Found M3-32-Meat Cooler Heat Detector was going in and out of trouble Due excessive condensation and EOL resistor being broken off causing trouble. Replaced EOL 47K ohm resistor and Reset system. Also Replaced water damaged Horn/Strobes in meat cutting and meat wrapping rooms. ***All systems Normal and Reset at this time ***
Semi-annual FM 200 suppression system inspections.
Completed Quarterly Inspections for both wet and dry sprinkler systems
Completed Annual Fire Alarm Inspection for 2017
Performed special hazard inspections.