Tyler did a great job
Very good service - tech was friendly, respectful of new pandemic procedures and thorough.
Thank you for going above and beyond replacing the tile in the ceiling that someone else did not replaced. It was greatly appreciated.
Do you fix the light issue?
Annual inspection of (3) FE's Portable Extinguishers Inspection
Kelly called - alarm panel in trouble needs service
SD MENS TRIANING ROOM: Smoke detector in MENS restroom on the 1st floor in the new addition was causing a ground fault on the system. Needs to be replaced. Simplex non-addressable. - repair
Bobbi called, said she needs service to check system -they are unable to reset it- it sent a comm fail after a test signal. they are in until 5PM- ask for Fred.
Per Ben Wright they have several FE that need to be inspected. He would like sticker tags as the standard tags have not been staying on for them
Emergency Service Call - Katie K called in- Lightning struck the building and now the fire alarm will not reset. Eric called in- said now they are showing a ground fault tbl- call 269-948-4800 option 1 to advise you are coming.
Annual Fire Alarm Inspection (80 devices)
Annual Fire Extinguisher Inspection (6 FEs) Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (3 FE) Annual Exit & Emergency Lighting Inspection (5 units) Portable Extinguishers and Emergency / Exit Lights Inspection
Alarm Systems Repair
Annual Fire Alarm Inspection (14 devices) Panel - DCS PC5010
Annual Fire Alarm Inspection (52 devices + 2 duct detectors) DMP XR500
Annual Fire Alarm Inspection (36 devices)