Bob was very knowledgeable and helpful. Got through the inspection quickly.
Alarm Systems Repair
ATTN: Mike Hill PH: (248) 212-6069 EMAIL: email@example.com . RE: FIRE PROTECTION DEFICIENCIES NOTED FROM INSPECTION . Mike, Thank you for choosing FIRE PROS, INC. as a service provider for your organization. We appreciate the opportunity to keep your facility fire safe and code compliant. During our recent inspection services, we noted an issue that requires additional attention in order to be brought back up to code compliance. Please see the description below and the total cost for the service. . Alarm Systems Repair Fire Alarm System: The Office Smoke Detector Device was tracked down and found above the Drop Ceiling and needs to be dropped down to its original location (see picture) - repair HD KITCHEN: Fire Alarm System: The Heat Detector Device in the Kitchen is showing signs of corrosion, and requires replacement - repair Inoperable Deficiency for SD OFFICE: Office smoke detector above drop ceiling 8-21-17 ALR/DV MOVED SMOKE Deficiency for HD KITCHEN: Heat detector shows
Fire Sprinkler System: Fire Pump Test Header Valve is cracked and requires replacement - repair Fire Sprinkler System: Systems 1, 2 and 10 have Outdated System Pressure Gauges (3 total) Fire Sprinkler System: Dry Sprinkler system has Outdated System Pressure Gauges (2 total)
Portable Extinguishers, Alarm Systems, and Kitchen Suppression Inspection
Portable Extinguishers, Alarm Systems, Kitchen Suppression, and Fire Door Inspection
Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (11 FE)