Give a raise!!
My experience was great, walked me through the process and was friendly and allowed me to ask additional questions regarding our location. Awesome job
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Gerald is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Completed annual Fire Extinguisher inspection for 2021
Portable Extinguishers Inspection
Completed Annual Fire Extinguisher Inspection for 2021
3/10 DO NOT MISS! Rescheduled due to FSM. notified Sarah and Brianna, store manager. She'll be there to let you in. km 3/3/2021 - Sarah (Corp.) called in to scheudle for 3/9/2021 at 9am. Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Semi-annual kitchen system inspection. Annual fire extinguisher inspection Annual Emergency/Exit Light Inspection (11) Deficiency: Kitchen suppression Ah Deficiency: Kitchen suppression Ansul (6) gallon Ah System is improperly manifolded needs to be corrected and add burst disc union System is manifolded with 101-30 needs to be double tank cartridge 230 nozzle over fryer #4 is improper needs to be 3N nozzle All 3N nozzles need to be dropped to max of 35” all nozzles currently set above 40” (4) 4” nipples (4) couplings (1) stick chrome (3) hours (1) svc call (1) fuel Recommend to add (2) swivel adapters to correctly aim nozzles Regulator is past due for hydro test needs replaced (2) hose kits are pas
Special Hazards Inspection