My experience was great, walked me through the process and was friendly and allowed me to ask additional questions regarding our location. Awesome job
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Gerald is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Scope of Inspection Semi-Annual Special Hazards System Inspection • Test the control panel functions to include the lamps and LED’s, check fuses, interface equipment and check the primary power. • Test smoke detectors by introducing approved aerosol into smoke detector chamber, or specific manufacturer recommended methods of performing the proper test and verify the proper signal was received at the alarm panel. • Clean all smoke detectors with nitrogen. • Test manual pull stations through a full range of motion and verify the proper signal was received at the alarm panel. • Test manual pull station to verify activation of the solenoid(s). • Activate the manual pull stations and abort switch to verify that the manual pull station will override the Abort switch. • The detection circuit is tested to ensure that cross zone activation will properly release the agent. • Cross zone the detectors and verify proper function of each abort switch. • Cross zone the detectors and verify time
Special Hazards Inspection