Great job, was here in a timely manner and spent time investigating and making sure staff understood how to operate the door/alarms properly.
Alex came in got the job done!
Emergency / Exit Lights Service Call Service call to verify ELight operational and clear deficiency.
Rick trouble on panel 810-293-7311 tamper fault - 810-293-7311
4/6 confirmed with Cathy 9am Alarm Systems Inspection
Portable Extinguishers Inspection
Replaced E AND F COURT SHOWER ROOM NURSE CALL PULL CORDS WITH CUSTOMER SUPPLIED STOCK AND TESTED. Also Trouble shot E8 Pull cords not functioning, Nurse Cord switches functions but Hall Annunciator not functioning when cords are pulled however Annunciator does function when other cords are pulled.
Talk to Jeff onsite Alarm Systems Service Call Crash bar is not functioning correctly wants us to take a look to quote what could be done and if it needs to be replaced.
Nurse Call Panel system Down upon arrival along with 6 Key Pads, Customer was changing out key pad and shorted power out that caused key pads on loop to loose power and nurse call system to crash. Checked system power supply fuses and attempted powering system down and back up. ***Informed Customer that he must contact Simplex to Assess this issue*** ***Nurse call system remains down and key pads remain w/out power***
Replaced Smoke Detector Bases In Rooms F9 and F8 that have Remote LED OUT Connections Tested smoke detectors in both rooms and verified Remote LED’s in hallway functioned and reset system. ***All Systems Normal and Reset ***
Exchanged E Court Laundry Extinguisher that was Discharged