was great service he was polite and on time.
Alex always does an excellent job
David did a great job servicing my sprinkler system. He was knowledgeable and willing to share his knowledge!
Andy was very thorough and took time to explain the what’s and why’s throughout the service. I really appreciate the information and how knowledgeable he is.
You can reach me on 810 441-2243 for a warranty visit
Great job, was here in a timely manner and spent time investigating and making sure staff understood how to operate the door/alarms properly.
Alex came in got the job done!
Annual Fire Extinguisher Inspection of 20 units (10) 1st 10 units @ base price $41.20 (10) additional units @ $1.03 Annual emergency/ exit lighting inspection (55) units @ $1.55 ea Semi-annual Kitchen Suppression System Inspection (1) Ansul R102 3 gal A-1 head @ $61.80 (2) 360 degree links changed @ $10 ea
Annual Fire Extinguisher Inspection of 24 units (10) 1st 10 units at base rate of $41.20 (14) additional units @ $1.03 ea Annual Exit & Emergency Lighting Inspection (46) units @ $1.55 ea Semi-annual Kitchen Suppression System Inspection (1) Ansul R102 3 gal A-1 head @ $61.80 (2) 360 degree links changed @ $10 ea
Portable Extinguishers Inspection
9/16/22 (EA) Techs are to call Josh 989-297-3452 when en route. Sprinkler Service Call 9/16/22 (EA) Per Josh, the riser room is over 150 degrees and there is boiling water coming from the fire pump. The air compressor is coming on frequently. Deficiency: Main fire pump controller is not responding to the stop 🛑 button to shut fire pump down this unit will have to be serviced to determine what relay is not operating properly there is also a trouble on the panel that says alarm relay.