Prompt, professional service.
Service was interrupted several times by "emergencies" in other areas thus making the overall job take longer.
The gentleman that came out was great, was able to get what we needed fixed. Very timely.
Thanks for your Quick service and professional work by Tyler
HS ROOM 1062: H/S in 1061 is bad and needs to be replaced. Simplex model 4906-9129 - We will need to remove the white plastic bezel and put it on the new one.
Annual Fire Alarm Inspection (511 devices) (Simplex 4100U)
Upon filling the sprinkler system, the technician found that the air compressor would not turn on ever with there being full power to it. With further investigation, the technician tapped the pressure switch and the air compressor turned on. This should not be how the compressor should be working. The pressure switch will need to be replaced.
Portable Extinguishers Inspection
Semi-annual Kitchen Suppression System Inspection (2 systems) Semi-annual Fire Extinguisher Inspection (3 FE) Semi-annual Emergency / Exit Light Inspection (7 units) Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection
Amy called in for emergency service - the smoke detector in one of the barrier free apartments went off last night and the only way to get it to stop going off was to take if down and remove a tab. now she needs someone out to see what they need to get a smoke detector in there. 269-353-4712
Annual Fire Alarm Inspection (349 devices)