very courteous and efficient
Answered all questions, friendly
AJ has been wonderful getting the trash at our new restaurant, on a scheduled and even getting it emptied from previous owners!
Fire Extinguisher Inspection (4 FE) Annual Emergency/Exit Light Inspection (6 units) Portable Extinguishers and Emergency / Exit Lights Inspection
Suggested for FACP MECHANICAL ROOM: Building 311 in fire panel control room there is a 10 foot ladder and a three shelf storage rack all blocking fire panel. These items at a minimum should be moved away from the front of the panel. Must have access to fire alarm control panel.
Deficiency for FACP MECHANICAL ROOM: Battery in control panel for building 312,314 needs to be replaced. Battery is split and voltage is at .4 volts.
Annual Fire Extinguisher Inspection (3 FE) Annual Emergency/Exit Light Inspection (6 units) Portable Extinguishers and Emergency / Exit Lights Inspection
Semi-annual Kitchen Suppression System Inspection ((2) PCL 1.6gal) Kitchen Suppression Inspection
Alarm Systems Service Call
Found bad panel in bldg. 310.