Great service once again by Mark. Highly recommend.
Jared with Fire Pros has always done a great job for us. 100% recommend
I was late getting into the building, but the tech was able to enter with another group and knew where everything was and conducted the inspection before I arrived. We appreciate his timely work and and letting me know there were no issues.
Very thorough and done quickly. Explained what he was doing and kept it clean.
Tech was very prompt and professional, great company all the way around, no complaints
Good experience, send again
Arrived on time. Both tech's were knowledgeable and helpful. Took the time to go over what they would be doing and showed us some things we can use going forward.
Mark is the best!
11/15/22 Confirmed with Gary for 11/23/22 at 10:00ish / Sent email regarding inspection DH Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System) 5-Year Internal Due: 2024 FDC Hydro Due: 2024
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected/serviced the fire sprinkler system at your establishment in accordance with NFPA guidelines. While inspecting/servicing your fire sprinkler system, it was determined to be "Non-Compliant". The attached proposal summarizes the non-compliance issues that were found during the inspection/service and the costs and actions needed to correct them. Fire Systems of Michigan strongly recommends that your sprinkler system is repaired so that it will become compliant. If obstruction is present, this can render the sprinkler system to not properly operate in the case of a fire. NFPA 25 (18.104.22.168) Inspection of the internal condition of piping shall be conducted at a minimum of every 5 years for the purpose of inspecting for the precedence of foreign organic and inorganic material. This is a safety hazard and may contribute to damage or injury to your property and individuals in the event of a fire. Please cont
11/1/22 Confirmed with Jim Pickell for 11/3/22 at 8:00am DH Sprinkler and Obstruction Investigation Repair 2ND-YEAR DEFICIENCY REPORTED: Remove and replace the outdated water gauges for both systems. NFPA 25 (22.214.171.124) Gauges shall be replaced every 5 years 2ND-YEAR DEFICIENCY REPORTED: The tech will install the missing main drain sign to properly identify system components. 2ND-YEAR DEFICIENCY REPORTED: The tech will install a spare headbox, sprinkler heads, and head wrench for system #1. 2ND-YEAR DEFICIENCY REPORTED: Perform a 5-year internal assessment of system piping that is due for both systems. If an obstruction is present, this can render the sprinkler system not properly operate in the case of a fire. 2ND-YEAR DEFICIENCY REPORTED: The tech will install the missing control valve sign for both systems. Deficiency for Dry Next to O.H. door 12: 5yr internal assessment of system piping is due. Deficiency: 5yr internal valve inspection is due on the FDC check valve, in pit