Response from Fire Pros, LLC:
Thank you Pamela for the feedback.
super friendly and willing to explain possible issues. knowledgeable
Kitchen Suppression Inspection
TD 2.4.20 Nancy confirmed reschedule @ 8a 2/3-Nancy confirmed the semi-annual kitchen suppression inspection/aware of alarms NW Kitchen Suppression Inspection Semiannual Kitchen Inspection Ansul R102-T9 (6)500 links (3)360 links (17)Nozzles
Alarm Systems Inspection
2/3-Chris confirmed (manager) NW Perform required 12 year hydrostatic test on the main hood kitchen fire suppression system except the actuation cartridge which will not be due until 2030. All work done in accordance with NFPA 17A. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to the deficiencies described below and may not properly exting