Appreciate the guys coming to our rescue.
They did a good job
Alex did great!
Sean did a good job. He should bring donuts the next time. lol
Sean was very Pleasant and professional.
Sean did good.
Came a day early. All that matters is the residents safety.
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Alex is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Per call from Stephen dry system issues. water is shut off
Re-Wired ( Zone 3 Sprinkler) Re-Ran approximately 15 feet 4/18 Fire Wire used 12 feet 3/8 inch flex with 2- 3/8 inch flex connectors. Re-Tested Zone 3 Completely and Reset system. (No Grounds present at this time ***All systems reset and normal at this time*** Found low air pressure switch was wired incorrectly was wired for high air pressure instead of low air switched wiring and tested.
Completed Emergency Sprinkler Service Call