Tech willing to explain system operation and minor problems that can occur
Alex was quick and efficient. After a little bit of confusion with a different tech, he came out and got it figured out.
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Alex is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Tech called before arriving to make sure it was convenient for him to come and do the work which is a big plus for me hopefully this will solve our problem
3/26-Zachary confirmed the kitchen suppression inspection/aware of alarms. Please see Sarah when you arrive/use backdoor. NW Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Deficiency: Small hood both fryers are undetected. Detection is in duct only. Deficiency: Electric non fuel source on deep fryer does not de energize upon fire system actuation. Suggested: Hood penetrations need to have quick seals installed.
Kitchen Suppression and Portable Extinguishers Inspection
Approved by Jeremy, manager Kitchen Suppression Inspection Semi-Annual Kitchen Inspection (4) R102-S-3
2/19-Akasha confirmed the semi-annual kitchen suppression inspection/aware of alarms. Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-S3 (Chase) (4)280 links (6)Nozzles Ansul R102-S (Chase) (3)360 links (4)Nozzles