Always prompted and take pride in the jobs
We've been using Fire Systems, and our tech, Jim, since I've worked here, and also at my last place of employment. Always friendly, professional, quick, and helpful. Can't think of a single thing I would change. This time, Jim was training another tech. Both were wearing masks and practicing social distancing perfectly.
He was very knowledgeable, shared all he was doing with us. Very fast and we definitely appreciate that
Jim is always very polite and answers any questions I may have. Always a pleasure working with Jim.
10/18 Confirmed with GM Courtney, she said they slow down around 2:00...KM Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen Inspection Ansul R102-S3 (Chase) (4)280 links (6)Nozzles Ansul R102-S3 (Chase) (2)280 links (4)Nozzles Ansul R102-S3 (Chase) (3)360 links (4)Nozzles Deficiency: Number of Systems failed : 3 Deficiency: Number of Extinguishers Left at Job: 1 Deficiency for Ansul (French Fry Hood) R-102 3 Gallon Chase: All three systems need to have horn/strobe added. No discharge warning device present. Deficiency for Ansul (French Fry Hood) R-102 3 Gallon Chase: Both fryer hood system have improper surface protection. Nozzles need to be changed. Deficiency for Ansul (Grill Hood) R-102 3 Gallon Chase: Clamshells are blocking grill protection . Deficiency: 10# abc fire extinguisher in store room needs a 6yr maintenance. Deficiency: No fire extinguisher by rear Kitchen Exit. Recommend 10# abc.
10/14/21 confirmed with Mia for Friday 10/15/21 sm Kitchen Suppression Inspection Semiannual Kitchen System Inspection
10/13/21 confirmed Via Email SM Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (2 FE)
10/13/21 confirmed with susan for Thursday n 10/14/21 . Kathy will put the alarms in to test SM Kitchen Suppression Inspection Semiannual Kitchen System Inspection Ansul R102-S3 (3)360 links (8)Nozzles
10/11 Confirmed with manager Kevin, they sometimes have a slow down around 9;00 - 10:00, so you should be good to do these Chase systems at this time.km Portable Extinguishers and Kitchen Suppression Inspection Deficiency: Number of Systems failed : 2 Annual Fire Extinguisher Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-S3 (Chase) (4)280 links (6)Nozzles Ansul R102-S (Chase) (3)360 links (4)Nozzles
Portable Extinguishers Repair
7/15/21 Confirmed with barb for Friday 7/23/21 , go in the Main fair Gate off Custer and Barb will be Waiting to let you in SM Kitchen Suppression Inspection Semiannual Kitchen Suppression Inspection FireSoft Due Date: 06/04/2019
7/2/21 need to Reschedule Friday 7/9/21 sM 7/1 Confirmed with Rich via emails. Colin will be on duty for you km Industrial/Dry Chemical Suppression Inspection Semi-annual Industrial System Inspection PyroChem PCI-35X2 (2)360 links (7)Nozzles
Completed quoted work