David is very knowledgeable took care of our problem and did a Great Job!
Always prompted and take pride in the jobs
We've been using Fire Systems, and our tech, Jim, since I've worked here, and also at my last place of employment. Always friendly, professional, quick, and helpful. Can't think of a single thing I would change. This time, Jim was training another tech. Both were wearing masks and practicing social distancing perfectly.
He was very knowledgeable, shared all he was doing with us. Very fast and we definitely appreciate that
Jim is always very polite and answers any questions I may have. Always a pleasure working with Jim.
10/6/22 Confirmed with Jim Y. for 10/10/22 at 11:00amish / Sent email regarding inspection DH Sprinkler Inspection Annual Sprinkler Inspection (1 Wet Sprinkler in Basement) Deficiency: There is no evidence of five-year internal pipe obstruction investigation. Deficiency: There is no evidence of five-year FDC check valve investigation. Deficiency: There is no evidence of five-year FDC hydrostatic test. Deficiency: Spare head box is missing head wrench. Deficiency: Pressure gauges are outdated.
Sprinkler Service Call Service to install an ESC