Robert was an excellent technician. He was very thorough. Also, the prices at Fire Pros are so reasonable.
Alex was very professional and nice.
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Alex is an awesome asset and we want to create value for you and your organization! In the meantime, please consider reviewing us on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
Extremely helpful and willing to explain
Alex was efficient and complete all inspection needed.
Alex, was helpful when answering questions about the inspection itself and best practices in the future.
Completed annual Fire Extinguisher and emergency light inspections for 2019 Exchanged 10 lb ABC in Basement Due for Hydro-Test and Mounted with New Bracket, Installed New 2.5 lb ABC in Van and Mounted Costumer supplied 2.5 lb ABC inside furnace closet. Work Approved by Elizabet Bojaj
Completed annual Smoke/Co Alarm inspection For 2019
Exchanged 2.5 LB ABC in 3rd Floor Maintnance Room Due for 6 year Maintenance
Completed annual Smoke/Co Alarm and Extinguisher inspections for 2019
Completed annual Fire Alarm inspection September for 2019
Replaced Dining Room Horn/Strobe and Tested also Cleaned 2nd Floor Hallway Smoke Detector and Reset System. ***All Systems Normal and Reset ***
Replaced Fitness Rm H/S
Completed annual Fire Extinguisher and Emergency Light Inspections for 2019
Completed annual Fire Extinguisher Inspection for 2019 Replaced Missing Laundry Room 10 lb ABC Extinguisher with New. Pre-Approved by Jim Humpal
Customer Put Battery In Backwards Corrected Battery Placement ***Detector is no longer beeping***
Annual Exit & Emergency Lighting Inspection (1 unit)
Completed annual Smoke Alarm/Emergency light and Extinguisher Inspections for 2019
REPLACED 2-120 VOLT INTERCONNECTED SMOKE ALARMS THAT WERE DEFICIENT FROM INSPECTION AND TESTED ***All Systems Normal and Reset ***
Arrived On-Site FACP was showing 20 Troubles and lobby and New Breakfast Area needed Horn/Strobes Installed. Trouble Shot 20 Troubles and Cleared All 20 Troubles. Re-Mounted Existing Smoke Detectors To Ceiling and already provided Drop Ceiling brackets. Provided and Installed and Wired 4 Wheelock Ceiling Mount Horn/Strobes and and Re-Installed and Wired 1 Existing wall mount Horn/Strobe. Tied all wiring into Existing system and Reset System ***All Systems Normal and Reset ***