Techs are awesome and very knowledgeable.
Response from Fire Pros, LLC:
We appreciate your feedback and 4 star review Jeff.
Getting a little slow on service. Seams like it takes a bit of time to get parts and return to complete the job.
Sean is a pleasure to work with. He is very knowledgeable and willing to help you understand the system for trouble shooting problems that may occur with the sprinkler system.
I like fire pros. The guys that come in know what they are doing but always seem to have fun while doing their job. It is enjoyable to work with them.
I think your company is lucky to have such a great employee!
Portable Extinguishers Installation
CHECKED CUSTOMER REPLACEMENT OF DIALER AND NAC PNL BATTERIES ALSO RE-LOAD TESTED FACP BATTERIES EVERYTHING PASSED WITHIN NORMAL LIMITS ***All Systems Normal and Reset ***
Industrial/Dry Chemical Suppression Inspection
1/31-Alberto Garcia de Alba confirmed the semi-annual kitchen suppression inspection/aware of alarms NW Kitchen Suppression Inspection ***NEW CONTRACT BEGAN 08/2019**** Semi-Annual Kitchen Inspection (1) Ansul 12 gallon system, Q-12 R102 Hood (1) Ansul 6 gallon system, R-6 R102 Hood Deficiency for Ansul R102 18G: Regulators and expellant hoses out of hydro date. Improper expellant cartridge in system. Deficiency for Ansul R102 18G: Improper protection over 10b range and tilt skillet on back side of main hood. Inoperable Deficiency for Ansul R102 18G: Electric fuel source and non fuel source under front and back side of main hood does not shut down during system actuation.