Sensitivity Testing and Alarm Systems Inspection
Annual Fire Extinguisher Inspection (6 FE)
Annual Fire Alarm Inspection (25 devices) (Notifier SFP 400B)
Smoke detector in basement fell off wall - needs to be fixed
Fire Sprinkler System: 5-year Internal Pipe Investigation is due, as required by NFPA 25 Code (serviced every 5 years) - perform Fire Sprinkler System: System Pressure Gauge is due for replacement, as required by NFPA 25 Code (replaced every 5 years) - replace Fire Sprinkler System: Outside Alarm (local Bell) did not operate properly upon System trip. We propose a service call trip in association with the previously mentioned items to troubleshoot the problem. If we can fix on site without materials - then we will at no additional charge. If more is needed - then we will quote a return trip to repair.