Paul 517-202-4820 - alarm trouble on panel zone 2 call him enroute he might want to meet you onsite.
Sensitivity Testing and Alarm Systems Inspection
Annual Fire Extinguisher Inspection (6 FE)
Annual Fire Alarm Inspection (25 devices) (Notifier SFP 400B)
Smoke detector in basement fell off wall - needs to be fixed
Fire Sprinkler System: 5-year Internal Pipe Investigation is due, as required by NFPA 25 Code (serviced every 5 years) - perform Fire Sprinkler System: System Pressure Gauge is due for replacement, as required by NFPA 25 Code (replaced every 5 years) - replace Fire Sprinkler System: Outside Alarm (local Bell) did not operate properly upon System trip. We propose a service call trip in association with the previously mentioned items to troubleshoot the problem. If we can fix on site without materials - then we will at no additional charge. If more is needed - then we will quote a return trip to repair.