Great company, come in an get job done.
I was able to schedule quickly and get the stuff done that needed to be done before I was out of office. They explained everything and made sure everything was back to normal before leaving.
Came early, explain stuff, told me what I need to know, and checked to make sure my alarms were good. :) In and out. Great experience
Response from Fire Pros, LLC:
Thanks the 5 star review.
Alex was awesome to work with nice guy very knowledgeable
Dan came in earlier than expected and updated our tags in about five minutes. He was friendly and fast. I did not have to worry about someone taking up my time. Very happy with Fire Pros!
10/8 Approved via text messages with Franciso km 10/8 LM on Keith's phone. Emailed Francisco k 3/31-Call in May to schedule per Francisco NW 3/30-Called/emailed Francisco to schedule NW Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Hood A (Downstairs Kitchen) Ansul R102-D6 (3)500 (1) 360 links (11) Nozzles Hood B (Downstairs Kitchen) Ansul R102-Q12 (5)500 links (3)360 links (20) Nozzles Hood C (Upstairs Kitchen) Ansul R102-T9 (4) 500 (5) 360 (12) Nozzles Hood D (Upstairs Kitchen) Ansul R102-T9 () 500 () 360 () Nozzles Deficiency: All 4 systems are out of hydro date. Deficiency: Exhaust fan on hood D not working prior to test. Deficiency for R-102 6G wall: Electric 110v outlets under hood A do not de energize upon fire system actuation. Deficiency: No audible alarms on all 4 systems. Deficiency: Deep fryer and char broiler under hood D is unprotected. Deficiency: No audible alarms on all 4 systems.
10/8 Francesco confirmed appt. Call his cell 30 minutes prior to arrival: 248-941-9397. He'll meet you on site. Tech arrrival between 10:00 and 11:00 AM. km 10/8 LM and emailed Keith km 9/17 LM for Keith on VM km 8/13 LM and emailed Keith km Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-T9 (3)500 links (3)360 links (17)Nozzles Ansul R102-S3 (3)500 links (2)360 links (10)Nozzles Ansul R102-D6 (3)360 links (9)Nozzles Ansul R102-S3 (2)500 links (6)Nozzles Inspect 1 Ansul 3 gallon system in Men's Grill (We didn't have time to do this system on Friday. Deficiency: 9 gallon system has red button automan and exposed expellant hose. Deficiency: All 4 systems are not tied into building alarm.
Annual Fire Extinguisher Inspection (3 units)