Great company, come in an get job done.
I was able to schedule quickly and get the stuff done that needed to be done before I was out of office. They explained everything and made sure everything was back to normal before leaving.
Came early, explain stuff, told me what I need to know, and checked to make sure my alarms were good. :) In and out. Great experience
Response from Fire Pros, LLC:
Thanks the 5 star review.
Alex was awesome to work with nice guy very knowledgeable
Dan came in earlier than expected and updated our tags in about five minutes. He was friendly and fast. I did not have to worry about someone taking up my time. Very happy with Fire Pros!
12/22 FM David called and required this repair be done ASAP to avoid shut down. Confirmed with Trang for 10:00 AM 12/29 km 12/1 Cancelled due to FSM tech calling in sick. EMailed and LM on Trang's cell. km Confirmed with Trang. She would like to make payments on this. She'll have her accountant call us tomorrow. km Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is m
Completed Annual Fire Alarm inspection for 2020
Portable Extinguishers Inspection
Emergency / Exit Lights and Portable Extinguishers Inspection
Alarm Systems Inspection
10/8 Approved via text messages with Franciso km 10/8 LM on Keith's phone. Emailed Francisco k 3/31-Call in May to schedule per Francisco NW 3/30-Called/emailed Francisco to schedule NW Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Hood A (Downstairs Kitchen) Ansul R102-D6 (3)500 (1) 360 links (11) Nozzles Hood B (Downstairs Kitchen) Ansul R102-Q12 (5)500 links (3)360 links (20) Nozzles Hood C (Upstairs Kitchen) Ansul R102-T9 (4) 500 (5) 360 (12) Nozzles Hood D (Upstairs Kitchen) Ansul R102-T9 () 500 () 360 () Nozzles Deficiency: All 4 systems are out of hydro date. Deficiency: Exhaust fan on hood D not working prior to test. Deficiency for R-102 6G wall: Electric 110v outlets under hood A do not de energize upon fire system actuation. Deficiency: No audible alarms on all 4 systems. Deficiency: Deep fryer and char broiler under hood D is unprotected. Deficiency: No audible alarms on all 4 systems.