I would be happy to use fire pros at any of our facilities!!
12/29 Approved by Becca, she's only there til noon. Please be prompt! KM Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to the deficiencies described below and may not properly extinguish, suppress or control a fire. This is a safety hazard and may contribute to damages and injuries to your property and individuals in the event of a fire.
12/11 LM on VM for Monday afternoon at 2:00 km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semi-annual Kitchen System Inspection Deficiency: Number of Systems failed : 1 Deficiency for Ansul R-102 3 Gallon right of hood: System has red button actuator with exposed expellant hose. Deficiency for Ansul R-102 3 Gallon right of hood: Hood penetrations do not have quick seals. Deficiency for Ansul R-102 3 Gallon right of hood: Improper nozzles over range. Deficiency for Ansul R-102 3 Gallon right of hood: System does not have a discharge warning device.
Portable Extinguishers Inspection
12/1 - Scheduled with Chuck mh Kitchen Suppression Inspection Semiannual Kitchen Inspection Deficiency: Number of Systems failed : 1 Deficiency for Ansul R-102 6G right hood: Ansul double tank cartridge out of hydro date.