Professional from start to finish.
Tyler was very professional, and very willing to answer any question I had.
Efficient and timely,
The guys were patient and courteous with staff and residents
easy to work with, good attitude,
Zack was fast and polite. He knew what he was doing and had no issues completing the work.
I like these guys
Inspected 2 fire extinguishers
Inspected 36 fire extinguishers
Completed quoted work
Per call from Kevin there is a small drip/leak above the drain cup for the dry system. The system pressures are normal. PLease look into what is causing the leak.
Remove and replace a section of the sprinkler piping in the attic of the F Hall Galley that has a leak. Dry Riser room, rear of the building: Remove and replace a section of the sprinkler piping and a fitting on the dry system that has a leak.
Non emergency called in by Kurt 269-547-8567. The panel is not allowing them to add people, Kurt would like us out to look at it and find out why.
Annual Alarm Inspection
remount three horn strobes in new ceiling. They are above the ceiling and marked where they are and where they go. See Delton warehouse manager. Keep your hands clean they have an open house next week and the tiles should not get dirty.
Finished inspection of fire extinguishers and emergency lights. Sue approved all batteries to be replaced as well as the exit sign and emergency lights to be replaced on site.
Annual Fire Alarm Inspection Ademco Vista-32B, 1 smoke, 2 HS Located in Riser Room Only testing the fire alarm devices- no security points per contract