Did a good job, was on time .
Robert is always friendly and professional and completes any service requests and orders quickly.
Great work and service. Robert was very professional and comprehensive with his work.
Alex did a great job working through the issues and getting the system back up and running. Thank you for sending him. Although we didn't find a root cause for the issue, we have a follow-up scheduled on site to determine next steps. Thanks Alex for all your work in the middle of the night!
Tony responded promptly and met me at the facility. He patiently explained what happened, potential causes and recommended next steps. I will request him for our upcoming annual inspection and even consider switching our fire protection service from our current provider to Fire Systems based on my positive experience. I appreciate he mentioned this is a service you provide.
Response from Fire Pros, LLC:
Thank you so much Kym for sharing your positive experience with our company and our technician. We appreciate your business.
7/31 Approved by Ahmed, prefers morning. km Industrial/Dry Chemical Suppression Inspection Inspection of (1) Industrial Dry Chemical Suppression Systems. Paint booth PCI-70 ABC Deficiency: PCI-70 tank due for 6 year maintenance. Horn/Strobe did not operate during system actuation.
Arrived On-site Customer states A Court Door was not arming. Found Loose Key Core in Vonduprin Checksit. Tightened Core and Armed Door and Tested. ***All Systems Normal and Reset ***
Portable Extinguishers and Kitchen Suppression Inspection
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected the fire extinguishers at your establishment in accordance with applicable state statutes, local fire codes and NFPA guidelines. While inspecting your extinguishers, they were determined to be "Non-Compliant" per local fire codes. The attached proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Please contact me as soon as possible to review the attached proposal and schedule the repair to your fire extinguishers. I look forward to working with you to bring your extinguishers into compliance. To discuss this proposal, please contact: Rob Harrison Phone: (616) 588-0746 Email: email@example.com EQUIPMENT REPAIR AGREEMENT This Agreement between FIRE SYSTEMS OF MICHIGAN (Company) and you (the Customer) provides for repair services only on the equipment indicated on the "Scope of Work" and "Services to Be Completed
Kitchen Suppression Repair Furnish necessary parts and labor to repair the following per manufacture specifications and code requirements: -- Perform (3) 12 year hydro-test on ansul 3 gallon cylinders -- Perform (1) 12 year regulator replacement -- Repair and re-run detection line that has failed due to grease buildup -- Replace duct and plenum nozzles clogged by grease _______________________________________________________________________________________________________ *** Customer must hire an electrician to shunt all electric under hood to simultaneously shutdown when fire suppression system is activated. *** Customer must contact hood manufacture or third party company to replace missing filters. This can cause excessive grease build up in plenum and heat build up leading to unwanted fire suppression system discharge. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in