2/7-Dan confirmed 734-478-7834/please start with extinguishers NW Kitchen Suppression Inspection Semiannual Kitchen System Inspection Ansul R102-S3 (2)360 links (6)Nozzles Deficiency: Shelf over Range/Griddle combo unit blocking protection.
Arrived on site found FACP Normal upon arrival, load tested FACP Batteries. Batteries failed load test and require replacement. Replaced 2-12 volt 7 ah batteries 4-4-19 ALR. ***All Systems Normal and Reset ***