2/9/21 confirmed with Chris for Tuhrsday 2/11/21. SM 2/4/21 Rescheduled with Colin for 10:00 2/9/21. Sm 1/29/21 Confirmed with Colin for Tuesday @1:00 PM. SM Portable Extinguishers, Emergency / Exit Lights, and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Annual Emergency/Exit Light Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-D6 (6)500 (1)360 (13)Nozzles Deficiency: Number of Extinguishers Left at Job: 5 Deficiency: Number of Systems failed : 1 Inoperable Deficiency: 3- Emergency Lights and 1- Exit/Emergency Combo Light needs batteries. Deficiency for Ansul R-102 6 Gallon Right of hood: Ansul system is out of hydro date. Deficiency: 1- k-class fire extinguisher due for hydro test. 5- 10lb abc fire extinguishers due for hydro test.