I highly recommend Fire Pros. They're a great company and hire fast, friendly, and knowledgeable employees.
Response from Fire Pros, LLC:
Thanks Jeff for the feedback and 4 star review.
I'm sorry, but I am going to be paying for two men on this service call who did not know what they were doing. I had to show them everything they had to do and I had to help.
Inoperable Deficiency: FACPIn building 280 is not operating properly and should be replaced. This is a small conventional notifier with two inputs and one output no relays no door holders. Checked batteries good charging circuit good board has a general trouble also flashes AC light with trouble light. Resistor off both zones and NAC output and panel still in trouble. Even though battery voltage and charging output was good I replaced batteries general trouble still persists picture is with new batteries and entire board resistor off and it is still in trouble. Deficiency: FACP in building 260 is not operating properly and should be replaced. This is a small conventional Mircom with five inputs and two outputs. No relays no door holders. This panel shows a battery trouble. Charging circuit is shot,There is improper low-voltage 20.6 V.Per customer batteries were just replaced batteries metered at 10 V and 8v.Also zone five is in trouble. I was able to read resistor from panel, so I res
Emergency / Exit Lights Repair
Fire Alarm Inspection Edwards E-FSC- 15-20 initiating devices, 15 A/v's
Inspected 2 extinguishers and 1 emergency light. Exchanged (1) 5# abc fire extinguisher for 6 year maintenance
Courtney 616-835-1068 Alarm keeps beeping tried to silence says system trouble
Portable Extinguishers Inspection