Our technician, Gary Beckon, was extremely knowledge and thorough in his work. We greatly appreciated the professionalism.
I highly recommend Fire Pros. They're a great company and hire fast, friendly, and knowledgeable employees.
Response from Fire Pros, LLC:
Thanks Jeff for the feedback and 4 star review.
Annual Fire Extinguisher Inspection (3 FE)
Remove and replace the flow switch on system #2 failed when tested. The switch did not set off the alarm as it should when there is water flow. NOTE: The fire sprinkler system will need to be drained for the switch to be replaced. Dennis Sullivan requested (3) bandaids to be dropped off so they can patch some pinhole leaks. This will be done in-house.
Portable Extinguishers Inspection
Inspected 16 fire extinguishers and installed (1) new 10# abc for additional coverage.
Inspected 2 fire extinguishers and 1 combo light. Replaced combo light on site.
Alarm Systems Inspection