Here early Very professional Very knowledgeable
Our technician, Gary Beckon, was extremely knowledge and thorough in his work. We greatly appreciated the professionalism.
I highly recommend Fire Pros. They're a great company and hire fast, friendly, and knowledgeable employees.
Response from Fire Pros & Fire Systems of Michigan:
Thanks Jeff for the feedback and 4 star review.
I'm sorry, but I am going to be paying for two men on this service call who did not know what they were doing. I had to show them everything they had to do and I had to help.
I don't know about the cost
I appreciated the thoroughness of the technician who came to inspect our sprinkler system as well as our fire extinguishers. He answered my many questions and made good suggestions.
Annual Fire Extinguisher Inspection 7
Portable Extinguishers and Emergency / Exit Lights Inspection
Annual Fire Extinguisher Inspection (2 FE) Annual Emergency/Exit Light Inspection (1 unit)
Deficiency for DD ROOF TOP UNIT: RTU has a duct detector that is bad and needs to be replaced. Replace w SYSTEM SENSOR D4120 Deficiency for DD ROOF TOP UNIT: RTUHas a bad duct detector that has went into alarm on two occasions.A replacement would be a system sensor D 4120.I bypassed this duct detector so RTU would continue working until a replacement can be installed.