I highly recommend Fire Pros. They're a great company and hire fast, friendly, and knowledgeable employees.
Response from Fire Pros, LLC:
Thanks Jeff for the feedback and 4 star review.
I'm sorry, but I am going to be paying for two men on this service call who did not know what they were doing. I had to show them everything they had to do and I had to help.
Annual Fire Extinguisher Inspection (3 FE)
Annual Fire Alarm Inspection (24 devices) (Fire Shield F5502) Good afternoon! Yes, that would be fine. If we are not around he can use my door code to enter the buildings which is 1557
This quote is for Fire Pros to replace the Fire Alarm Panel in building 270 due to lightning damage.
Inoperable Deficiency: FACPIn building 280 is not operating properly and should be replaced. This is a small conventional notifier with two inputs and one output no relays no door holders. Checked batteries good charging circuit good board has a general trouble also flashes AC light with trouble light. Resistor off both zones and NAC output and panel still in trouble. Even though battery voltage and charging output was good I replaced batteries general trouble still persists picture is with new batteries and entire board resistor off and it is still in trouble. Deficiency: FACP in building 260 is not operating properly and should be replaced. This is a small conventional Mircom with five inputs and two outputs. No relays no door holders. This panel shows a battery trouble. Charging circuit is shot,There is improper low-voltage 20.6 V.Per customer batteries were just replaced batteries metered at 10 V and 8v.Also zone five is in trouble. I was able to read resistor from panel, so I res
Emergency / Exit Lights Repair
Fire Alarm Inspection Edwards E-FSC- 15-20 initiating devices, 15 A/v's
Inspected 2 extinguishers and 1 emergency light. Exchanged (1) 5# abc fire extinguisher for 6 year maintenance
Courtney 616-835-1068 Alarm keeps beeping tried to silence says system trouble