Re-Connected Horn/Strobe that Fire Department Disconnected ***All Systems Normal and Reset ***
Completed Annual Fire Alarm inspection for 2018
Test Header control valve handle missing, valve shall be replaced. - repair Repair of Gauges are outdated and shall be removed and replaced with new. Total: 13 Repair of Pipe that goes to out side damaged, when flowing ITV #2,#3 floods back area, pipe shall be replaced.
Completed Annual Fire Alarm Inspection for 2017