The guys were very friendly, Helpful in learning more about how to solve our problem we had! Would highly recommend them to other companies!
Alex is always thorough and concise! Vary happy with his service!
Alex is always available to assist whenever i have an issue
Alex is always available to assist whenever a issue arises
In my experience working with Fire Pros service staff I lost prefer Alex. He is articulate, thoughtful, thorough, accurate and efficient. He is also easy to talk with and friendly.
The guys that came out were very friendly, helpful and knowledgeable. We would be glad to have them back for future needs
Annual Fire Extinguisher Inspection (8 FE)
Annual Fire Extinguisher Inspection (2 FE)
Portable Extinguishers Inspection
Wet: Remove and replace (14) corroded sprinkler sidewall heads found throughout the building. **Please Note: The pricing provided in this quote excludes any repairs that may be necessary due to removing the existing sprinkler heads such as piping, fittings, and Drywall, to name a few. This quote covers only the material and labor to remove the current sprinkler heads and install new ones. Any patching of the access holes will be the responsibility of the customer.** NFPA 25 (18.104.22.168.1) Any sprinkler that shows signs of any of the following shall be replaced; (2.) Corrosion that is detrimental to sprinkler performance. Wet: The pump is not operations when the technician conducted the flow test. The pump did not kick on and the breaker kept popping. The customer will need to contact an electrician to troubleshoot why the breaker kept popping when it was reset. PER MIKE: they have installed a new breaker and is requesting we test the fire pump to make sure everything is working prope