Alex is always thorough and concise! Vary happy with his service!
Alex is always available to assist whenever i have an issue
Alex is always available to assist whenever a issue arises
In my experience working with Fire Pros service staff I lost prefer Alex. He is articulate, thoughtful, thorough, accurate and efficient. He is also easy to talk with and friendly.
The guys that came out were very friendly, helpful and knowledgeable. We would be glad to have them back for future needs
Arrived On-Site Nurse Call system was powered down. Re-Applied power, and Reset Call lights that were tripped on panel. Also explained nurse call system to staff member. System is Reset and Normal.
Arrived On-Site Front Door Power Supply was without Power. Checked breaker Panels Located breaker in Mechanical Room (Panel B Circuit 2 Labeled Outlets in Living Room) was Switched off. Turned breaker back on. Power Supply has power and front door Vonduprin bar is functioning. Tested bar and reset. ***All Systems Normal and Reset ***
Corrected Deficiencies from recent inspection Replaced 12-135 Fixed Heat Detectors and Tested ***All Systems Normal and Reset ***
Deficiency: THE FOLLOWING BATTERIES FAILED LOAD TEST AND REQUIRE REPLACEMENT FACP 2-12 volt 18 ah F2 NAC PNL 2-12 volt 12 ah
Fire Alarm Inspection (6) mp, (11) sd, (5) DD with test rest switches, (18) hd, (4) beam detectors. Need 12 foot ladder.
Completed Bi-Annual Smoke Detector Sensitivity for 2020
Arrived On-Site FACP Stated All Systems Normal and Reset. Viewed History. It stated NAC 2 was tripping and resetting in and out of trouble. Trouble shot Circuit, found H/S in Hallway by Room 118 was loose from base (loose enough that it pulled right off base like someone purposely disconnected it). Re-Secured H/S and checked rest of 1st Floor. All were secure. Metered circuit. Circuit is now well within normal parameters. Re-Connected circuit and Reset FACP. ***All Systems Normal and Reset*** (Will Monitor System over night to see if trouble re-Triggers.)
Per Aaron needs to be FE exchanged used in a trash fire
Alarm Systems Inspection
Inspected 2.5 lb ABC in Van and Exchanged Extinguisher Due to it being Due for its 6 year Maintenance
Completed Annual Fire Alarm inspection for 2020