2/25/21 confirmed WITH frank FOR 3/4/21 Pepe WILL PUT THE SYSTEM IN TO TSET. sm Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Deficiency: Number of Systems failed : 1 Deficiency: Salamander on main hood is unprotected. Deficiency: Salamander on main hood is partially outside of hood. Deficiency: Penetrations on main grill stand hood and fryer hoods need quick seals installed. Deficiency: Four holes in main hoods need to be plugged Deficiency: Main system control head does not have black box around it.