Did a great job of checking out the store! Friendly fast service.
Emergency / Exit Lights and Portable Extinguishers Inspection
Alarm Systems Inspection
Suggested: 2 of the 3, 120 smoke alarms are outdated and should be replaced.1st and 3rd floor smoke alarms are outdated and should be replaced.
Annual Fire Alarm System Inspection
Suggested: DD is local and has no cover. has been reported since 2016 at least
Return 3 FE from inspection on 4-20
Annual Fire Extinguisher Inspection (11 FE) Annual Exit & Emergency Lighting Inspection (7 units)
Annual inspection of 8 Fire extinguishers Annual inspection of 13 emergency/exit lighting units
Portable Extinguishers Inspection
Performed 5 years and deficiency repairs.
Craig called (231-629-1276) said they have a box for an emergency exit door going off- it's located above the ceiling in the weight room.
scheduled w/ Jaqueline 8am 11-28
Performed deficiency repairs on sprinkler system