Shout out to Alex Roths very nice, professional , shows up on time fast service . Great company to do business with couldn't be happier!!!
Alex was great, courteous and very professional would recommend him and Fire Pros!!
Compl annual Fire Extinguisher inspection for 2021
6/3/21 confirmmed with Denise for Thursday 6/10/21 sM Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Ansul R102-D6 (2)360 links (8)Nozzles Annual Fire Extinguisher Inspection
Corrected Deficiencies from recent inspection
4/14 Confirmed with Rick km Emergency / Exit Lights and Portable Extinguishers Inspection Annual Emergency/Exit Light Inspection Annual Extinguisher Inspection ( 5 ABCs ) Deficiency: Number of Extinguishers Left at Job: 2. 1. 10LB due for 6 year maintenance 1. 10LB due for hydro testing.
Completed Annual Fire Extinguisher Inspection for 2021
3/1/21 Confirmed Olga for 3/2/21 Tuesday. SM 2/15/21 Called and left VM SM Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (17) ABC? (1)K?
2/4Confirmed with Judy. Check in with main office upon arrival km Kitchen Suppression Inspection Semi-annual Kitchen System Inspection Ansul R102-S3 (2)360 links (6)Nozzles Deficiency: Number of Systems failed : 1 Deficiency: No audible alarm attached to system per Napa 17a unused micro switch is available Deficiency: kitchen suppression ah improper coverage over 6 burner range currently (2) 245 nozzles cannot have backshelf....backshelf doesn't seem to be removable (3) 1F nozzles (1) svc call (2) hours misc t and 90 all chrome Deficiency: kitchen suppression ah improper coverage over 6 burner range currently (2) 245 nozzles cannot have backshelf....backshelf doesn't seem to be removable (3) 1F nozzles (1) svc call (2) hours misc t and 90 all chrome penetration in hood needs plugged (1) plug