Mike did a great job when he was here and worked with us to make it a smooth morning.
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Mike is an awesome asset and we want to create value for you and your organization! In the meantime, please consider reviewing us on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
EMCOR Paperwork Attached Annual Fire Alarm Inspection
SD BEDROOM #3: 3 of the older ESL smoke detectors were out of sensitivity range and need to be replaced. Bedroom 3, Bedroom 4, and In hall by room 6. Can be replaced with 2WB. - repair
Annual Fire Alarm Inspection (7 devices) (ESL 1500)
Sensitivity Testing (16 devices) done in 5-2018 due 5-2020 For sensitivity testing- To do smoke sensitivity for model 429c use a magnet and count the number of flashes on the smoke LED. For 2WB use the i3 tool Annual Fire Alarm Inspection (30 devices) (Edwards 2400)
Inspected 23 fire extinguishers. Need to return and inspect townhouses since they need to inform tenants. Swapped out 3 extinguisher for hydro(2) 10#s and (1) 5# all abcs.
Stand Alone smoke detector East bedroom #1: SMOKE DETECTOR IN EAST BEDROOM IS DATED 2000 AND IS 18 YEARS OLD, RECOMMEND REPLACING IT. - repair
Stand Alone Smoke Detector Testing (5 Units)
Annual Fire Extinguisher Inspection (11 FEs) Annual Exit & Emergency Lighting Inspection (3 EEs)
Semi-annual kitchen suppression inspection Annual Emergancy/Exit Light inspection 8 Annual Fire Extinguisher Inspection 5
DIV3=test stand alone smokes annually (8 detectors)
See Tiffany - they used to put a magnet on a strip above fire panel to do a drill test. The magnet is there but does not work after the panel was replaced in June. See if we can hook up the magnet to do drills OR show her how to do a drill from new panel. Write up instructions when done. Also check zone 4 , it was in trouble but cleared when she hit the reset button. See Tiffany on site .
EMCOR Paperwork Attached Annual Fire Alarm Inspection (51 devices)