Mike did a great job when he was here and worked with us to make it a smooth morning.
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Mike is an awesome asset and we want to create value for you and your organization! In the meantime, please consider reviewing us on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
DIV3=test stand alone smokes annually (8 detectors)
See Tiffany - they used to put a magnet on a strip above fire panel to do a drill test. The magnet is there but does not work after the panel was replaced in June. See if we can hook up the magnet to do drills OR show her how to do a drill from new panel. Write up instructions when done. Also check zone 4 , it was in trouble but cleared when she hit the reset button. See Tiffany on site .
EMCOR Paperwork Attached Annual Fire Alarm Inspection (51 devices)
Deficiency for FACP KITCHEN: FACP IS STUCK IN BATTERY TROUBLE. CHARGING CIRCUIT IS AT 25.2,I REPLACED BATTS, THEY ARE 12.7/12.8VOLTS. PANEL WILL STILL NOT CLEAR. TRIED TO POWER CYCLE PANEL BUT STILL STUCK IN TROUBLE. I RECOMMEND REPLACING THE FACP. Deficiency for FACP KITCHEN: FACP IS STUCK IN BATTERY TROUBLE. CHARGING CIRCUIT IS AT 25.2,I REPLACED BATTS, THEY ARE 12.7/12.8VOLTS. PANEL WILL STILL NOT CLEAR. TRIED TO POWER CYCLE PANEL BUT STILL STUCK IN TROUBLE. I RECOMMEND REPLACING THE FACP. 1 NAC, 4 ZONES. FIRELITE MS-4
Annual Fire Alarm Inspection (30 devices) (Edwards 2400)
Annual Fire Alarm Inspection (7 devices) (ESL 1500) Sensitivity Testing (2 smoke detectors) done in 2017- due in 2019 To do smoke sensitivity use a magnet and count the number of flashes on the smoke LED.For smoke model 429c For 2WB use the i3 tool
Portable Extinguishers Inspection
Alarm Systems Inspection