Mike did a great job when he was here and worked with us to make it a smooth morning.
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Mike is an awesome asset and we want to create value for you and your organization! In the meantime, please consider reviewing us on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
Portable Extinguishers, Emergency / Exit Lights, and Kitchen Suppression Inspection
Portable Extinguishers and Fire Hose Inspection
Deficiency for SD DINING BATTERY OP: Dining room smoke detector is broken and should be replaced
Deficiency for SD NORTH BEDROOM BATTERY OP: Smoke detector in north bedroom missing,customer will replace. Deficiency for SD SOUTH BEDROOM BATTERY OP: SD IN SOUTH BEDROOM IS 10 YEARS OLD. DUE FOR REPLACEMENT. Deficiency for SD DINING BATTERY OP: Dining room smoke detector is broken and should be replaced
Sensitivity Testing (12 devices) Annual Fire Alarm Inspection (19 devices) (Firelite MS4)
EMCOR Paperwork Attached Annual Fire Alarm Inspection
SD BEDROOM #3: 3 of the older ESL smoke detectors were out of sensitivity range and need to be replaced. Bedroom 3, Bedroom 4, and In hall by room 6. Can be replaced with 2WB. - repair
Annual Fire Alarm Inspection (7 devices) (ESL 1500)
Sensitivity Testing (16 devices) done in 5-2018 due 5-2020 For sensitivity testing- To do smoke sensitivity for model 429c use a magnet and count the number of flashes on the smoke LED. For 2WB use the i3 tool Annual Fire Alarm Inspection (30 devices) (Edwards 2400)
Inspected 23 fire extinguishers. Need to return and inspect townhouses since they need to inform tenants. Swapped out 3 extinguisher for hydro(2) 10#s and (1) 5# all abcs.
Stand Alone smoke detector East bedroom #1: SMOKE DETECTOR IN EAST BEDROOM IS DATED 2000 AND IS 18 YEARS OLD, RECOMMEND REPLACING IT. - repair
Stand Alone Smoke Detector Testing (5 Units)