Sean did an excellent inspection. He was thorough and efficient.
When I mentioned that I almost always run into the extinguisher in its current placement, the tech offered to move it for us while he was here to rechargs the extinguisher. Thanks!
Robert was very nice and courteous,He knew what he was doing and talking about
Jared came back to my property to install all our new fire extinguishers in our end rooms. Jared was fast but very efficient getting the job done. Jared was friendly and knowledgeable once again during the install. I will recommend you all for years to come!
I've been in the property management business for almost 10 years and the Fire systems tech Jared that came out to my property was the BEST!!! he was friendly and professional and very knowledgeable in his work. I will definitely be referring Fire Systems to friends and family in the business.
Always good at calling and scheduling appointments and keeping our maintenance schedule worry free!
Thank you for your service Jared!
Sean was very nice to work with very professional and personable.
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Sean is an awesome asset and we want to create value for you and your organization! In the meantime, please consider reviewing us on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
Everything went great !
Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (2 FE) 3/15/21 confirmed with Micheal for 3/22/21 SM
3/12 Confirmed with Donna. Understands no cooking and alarms. km Kitchen Suppression and Portable Extinguishers Inspection Semi-annual inspection of PCL 300/300 hood suppression system. Annual Fire Extinguisher Inspection
need little giant for e lights in dining room 3/2/21 Confirmed with Tim for Thursday 3/4/21 SM Emergency / Exit Lights and Portable Extinguishers Inspection Annual Emergency/Exit Light Inspection Annual Fire Extinguisher Inspection (3)ABC Inoperable Deficiency: 2- Emergency Lights have dead batteries. 1- Exit/Emergency combo light has dead batteries. 1- emergency light has burnt out bulb.
2/26 Confirmed with Shannon km Portable Extinguishers Inspection Annual Extinguisher Inspection (11 Portable Extinguishers) Deficiency: Number of Extinguishers Left at Job: 3 Deficiency: 1- 10# abc fire extinguisher due for 6yr maintenance. 2- 10# CO2 fire extinguishers due for hydro test.
Completed Annual Fire Extinguisher and Emergency light Inspections for 2021