he was very patience with me being a new employee. explaining everything in great detail
Great speedy response to our emergency...and such a friendly staff!
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Alex is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Alex always does a fantastic job!!
Alex always does a great job each time he comes out to provide service for our community, he is always professional and provides quick and qualitative solutions to any issues that arise. When Alex walks thru the door we know that we are in great hands and that the job will be done right!
The service was fast and professionally quality.
Response from Fire Pros Inc:
Thank you for leaving a review, we greatly appreciate your feedback! Alex is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day!
Great work and Wonderful work and fast job
Alex was very professional and knowledgeable. He made sure to check all doors and to make sure they were secure before he left the community.
The response was swift and fast.
I am very happy with I am very happy with the work that she has done today. Thank you
Trouble Shot System. System Normal upon Arrival. There are 19, 194 Fixed Heat Detectors in attic. Checked all 19 Heat Detectors for signs of water damage. No damage present. However found some wiring staples that had penetrated outer wiring jacket, but did not see any penetrations through the actual wire touching the copper. I can not rule out the wiring yet. I have strapped out the module removing the heat detector wiring from the module. (Will check back in a week from now if there has been any alarms or troubles with the attic heat Detectors) if there’s an Alarm then the module will require replacement. If not then we will quote time and labor and material to replace the wiring in the attic to all the heat Detectors.
Arrived on site found FACP showing earth ground on internal SLC. Trouble Shot wiring to Elevator mechanical Room in Garage. Found niks in wiring between junction boxes for elevator recall. Re-Ran wiring between boxes and Reset System. No Grounds present and system is normal and reset.
Replaced Dish Washer Room Heat Detector and addressable base and Reset System. ***All systems Normal and Reset ***
Gathered Information for Dish washer Room Heat Detector Replacement System will remain in trouble until Heat Detector is Replaced.
Dropped off Spare Replacement Head For Room 433 That was Claimed to have been lost. Located missing head found in dresser drawer. Cleaned head and replaced. All systems normal and reset ***.
Dropped off Replacement Head For Room 433 EST Dealer Has to program Unit due to Panels automatic mapping is not turned on.
Thank you for
Portable Extinguishers, Kitchen Suppression, and Emergency / Exit Lights Inspection