The service team was responsive and easy to work with. Re-scheduling the service went smoothly and was done in a timely fashion.
Great service very professional technician Alex is very experienced and thoughtful as well as professional
Alarm Systems Service Call
Alarm Systems Service Call check system - not sending test signals CMS acct# FLV90335 - in CMS as Shogun Restaurant
3/9-Phillip confirmed both alarm tech/electrician will be there between 9-10 AM NW Replace bad kitchen fire suppression system control head with new. Upon approval customer will need an electrician to disconnect the electrical and fire alarm from the kitchen fire suppression system and then reconnect upon installation of the new control head. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen s
Annual Alarm Inspection Inoperable Deficiency: Both tamper switches at the riser need replacement. Both damaged and bypassed at the switch with a resistor. 2 @ System Sensor Model PSP1 will be needed. Rope Style
Met with Rob was informed that fire marshal wanted FACP Supervisory RTU 1 Cleared. When arrived on-Site FACP Stated no supervisory’s and RTU-1 was reset on 2-24-20 @ 1359. However on 2-13-20 Telephone line 2 (blue-blue white/and orange-orange white pair of CAT5 wires are dead at FACP with no Dial tone or voltage. And requires to be addressed by telephone provider.