TJ has an awesome personality and very knowledgeable about the job.
Mark was concerned about my problem , called the next day to see how things were
bob has always done us a great job,, he represents himself well ,,, and does the same for fire pro's, ,great guy ,great service
The service team was responsive and easy to work with. Re-scheduling the service went smoothly and was done in a timely fashion.
Great service very professional technician Alex is very experienced and thoughtful as well as professional
11/1/23 Confirmed with Geoffry for 11/3/23 at 8:00am DH / Sent email regarding Inspection DH Sprinkler Inspection Annual Sprinkler System Inspection (1 Wet)
11/1/23 Called site regarding inspection DH Sprinkler Inspection Annual Wet Sprinkler Deficiency: The quick response sprinkler heads are from 2001. They are the old recalled central sprinkler heads so spell the heads must be tested by you all laboratories removal of some heads will be necessary for testing. 4-155° chrome pendant sprinkler head half inch orifice Deficiency: This job is a two-man job due to the tightness of the piping. You’ll have to have one small man they can crawl up in under in by piping and another man on the outside to make sure he is safe and to hand him what he needs. There is no evidence of fire sprinkler system, internal obstruction, investigation of piping. We will need one 4” by 3 inch Victaulic coupling 2-men Deficiency: There is no evidence of five-year internal inspection connection check valve. 2- 4” vic couplings Deficiency: There is no evidence of five-year Hydro test on fire department connection Deficiency: There is no evidence of internal in
9/27/23 Confirmed by Clara for 10/4/23 between 9-3pm DH / Sent email regarding inspection DH Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System)
Sprinkler Inspection Quarterly Sprinkler Inspection ***COMMERCIAL FIRE PAPERWORK***