The service team was responsive and easy to work with. Re-scheduling the service went smoothly and was done in a timely fashion.
Great service very professional technician Alex is very experienced and thoughtful as well as professional
3/9-Phillip confirmed both alarm tech/electrician will be there between 9-10 AM NW Replace bad kitchen fire suppression system control head with new. Upon approval customer will need an electrician to disconnect the electrical and fire alarm from the kitchen fire suppression system and then reconnect upon installation of the new control head. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen s
Annual Alarm Inspection Inoperable Deficiency: Both tamper switches at the riser need replacement. Both damaged and bypassed at the switch with a resistor. 2 @ System Sensor Model PSP1 will be needed. Rope Style
Met with Rob was informed that fire marshal wanted FACP Supervisory RTU 1 Cleared. When arrived on-Site FACP Stated no supervisory’s and RTU-1 was reset on 2-24-20 @ 1359. However on 2-13-20 Telephone line 2 (blue-blue white/and orange-orange white pair of CAT5 wires are dead at FACP with no Dial tone or voltage. And requires to be addressed by telephone provider.
Portable Extinguishers and Kitchen Suppression Inspection
Alarm Systems Service Call Deficiency: Replaced batteries in main panel due to age. 2@ 12 volt 7 amp hour. Suggested: Customer would like a quote to have a new Fire Alarm System installed. Site visit would be needed.
Fire alarm troubles Account: 6955112 Password: Happy Week Alarm Systems Service Call
2/10-Rob (GM) confirmed the kitchen suppression inspection/aware of alarms NW Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-D6 (3)500 links (2)360 links (10)Nozzles Ansul R102-S3 (2)500 links (6)Nozzles Annual Fire Extinguisher Inspection
2/11-Need Heat Gun-Phillip confirmed the semi-annual kitchen suppression inspection/aware of alarms NW 2/10-Emailed Phillip to schedule NW Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection PyroChem PCL-460/460 (8)500 links (2)360 links (20)Nozzles Range Guard RG-1.25 (2)Nozzles (Test via 325 degree heat sensor outside of hood - no fusible links) (3rd system unknown) Inoperable Deficiency: Pyro Chem control head does not release with detection. System is manual release only. Control head was missing cover and cartridge plate upon arrival.
2/6/2020 - Chris called back to scheduel, he will take care of the alarms. 2/6/2020 - LM on Chris' VM (Cell). Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection
Alarm Systems Service Call