Jarrod from Fire Systems of Michigan serviced our fire extinguishers at our facility and I cannot be more satisfied. He was very kind and knowledgeable. He spent time to show me what to look for to keep our animals and staff safe in the case of a fire.
Prompt and professional.
We had our annual fire extinguisher inspection today. It is always a pleasure to have this completed by Jared. He is extremely knowledgeable and efficient.
Arrived on time! Was very thorough on coaching staff on how to use the alarm system in every possible scenario!
He was a great technician he checked everything on all our fire extinguishers very detailed on all his work while being a true professional thank you very much please send him back next year
Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System) 5-Year Internal Due: FDC Hydro Due:
8/9/23 Sent email regarding Inspection DH Sprinkler Inspection Quarterly Sprinkler Inspection
8/15/23- confirmed with Daniel Young 8/9/23 Sent email regarding inspection DH Sprinkler Inspection Quarterly Wet Sprinkler Inspection
8/11(TJV)- confirmed appt via email with Nicole to arrive between 8am-9am Riser is located in corner of warehouse. SP monitoring alarm panel is located in office electrical / phone room. Sprinkler Inspection Annual Fire Sprinkler System Inspection Deficiency: There is no evidence of fire department connection hydrotest Deficiency: There is no evidence of fire department connection check valve internal inspection 🧐 2- Victaulic couplings 4” Deficiency: There is no evidence of five-year internal obstruction investigation. 1- man lift 2- Victaulic couplings Deficiency: Sprinkler system the signs on all the valves. Two main control valve signs one main drain sign one inspectors test sign. Deficiency: Five-year internal inspection 🧐 alarm valve needs to be done. Gasket material
8/3/23 Confirmed with Kim for 8/3/23 at 12:00pmish DH 7/18/23MV Emailed Kimberly regarding inspection date 7/26, Kim confirmed Conformed with Sprinkler Inspection Annual Sprinkler Inspection (12) Limited Area Sprinkler Systems Deficiency: All the sprinkler heads in this facility are more than 50 years old and must be tested one head per building. 12- 1/2” 155° chrome pendant sprinkler heads will be needed for testing.
8/2/23 Confirmed with Travis for 8/3/23 DH Sprinkler Inspection Annual Sprinkler System Inspection Deficiency: Three sprinkler heads one in freezer to in cooler are due for replacement. 3- 286 degree chrome pendant dry barrel sprinkler heads 12”