Very pleasant! Knew his job!
Completed Annual Fire Alarm Inspection for 2018
Reset deluge system that had gone into alarm
Corrected Quoted Deficiencies from Fire Alarm Inspection ***All systems are normal and reset ***
Installed Strobes to new science class rooms that are compatible with existing system and tested system ***all systems normal and reset at this time ***
Dear Mike, Thank you for choosing Fire Pros, Inc. as your fire protection service provider. We propose an additional trip back to this location to fix the deficiencies found during our latest inspection/service call of your fire alarm system. Our technician found a number of audio/visual devices (horn/strobes) not working at all. They traced the problem back to a bad "signal" card inside the main control panel. This devices needs to be replaced to have the output voltage to fire the horn/strobes. The specific parts needed and the investment schedule is listed below. FIRE PROS, INC. is fully insured and licensed. We are able to provide fast efficient 24-hours a day service. Our customer service philosophy is to provide the assurance that your building and those you employ and serve are protected by properly maintained and code compliant fire protection equipment. We appreciate your kind consideration of our proposal and welcome the opportunity to submit future proposals for any other fi
7/24/17 ADD TWO CEILING MOUNT HORN/STROBES TO SCIENCE ROOM. DROP CEILING. TIE TO EXISTING WIRING ALREADY IN ROOM. Alarm Systems Service Call Add Simplex H/S to ceiling in new Science Room.
Fire Sprinkler System: The Air Compressor for the Pre-Action system is seized up and will no longer operate - replace Fire Sprinkler System: (3) Outdated System Pressure Gauges on the Pre-Action system located in mechanical room across from gym by pool reception office - replace
Replaced 2 FACP batteries and 2 NAC PNL 8 batteries that failed load test
Replaced NAC panel 2 batteries that failed load test
Kitchen Exhaust Cleaning Cleaning
Completed Annual Fire Alarm Inspection for 2017
Pulled 4 dry pendants in cooler for testing.