Friendly, Polite, and Professional!!
Jared was Awesome! Great Customer Service and went above and beyond to correct the errors from past employees.
Fixed Extinguisher bracket and serviced extinguishers in a very timely fashion.
Matt did a great job installing the extinguishers and answering questions on additional services that our company may require. Thanks for a job well done.
Obstruction Investigation, Sprinkler, and Hydrostatic Testing Repair
6/29/2020 - 1:41pm Appointment approved by Chris (Mgr) for 6/30/2020 at 1pm. He will be ther along with Tammy (SM). 6/25/2020 - 3:52pm Tim Thurman (Owner) verbally approved the quote. He also needs e-light work done. (1) by the bathrooms and (1) over the front door on Washtenaw side. Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to the def
Alarm Systems Service Call Jeff called needs someone to check system showing tbl 1E346 tamper switch- going in and out of trouble
Corrected Deficiencies from 2019 Emergency light inspection and Updated 2019 Inspection Report
INSTALLED NEW 2.5 lb ABC IN VAN AND UPDATED 2019 INSPECTION REPORT
Replaced FACP Batteries that were Deficient from recent Inspection & Updated Report ***All Systems Normal and Reset ***