Fixed Extinguisher bracket and serviced extinguishers in a very timely fashion.
Matt did a great job installing the extinguishers and answering questions on additional services that our company may require. Thanks for a job well done.
Annual Fire Extinguisher Inspection (4 FE)
Annual Fire Alarm Inspection (11 devices) (Edwards 5751-B)
Smoke Detector in 2nd Floor 2CW Electrical Room was in Alarm. attempted Cleaning Smoke/Heat Detector. Smoke/Heat Detector Continues to go into Alarm. Smoke/Heat Requires Replacement. (Siemans FP-11 Address 3-004) Customer will contact Siemans to order Replacement. System will remain in trouble until Smoke/Heat Detector Head is Replaced Head is Temporarily Removed to Reset System.
Fire Alarm System Normal.Pug In Wall Style CO Det was beeping causing nuisance signal Due to low battery after Replacement of battery unit still chirps and requires replacement. Customer will replace unit
Completed Annual Fire Alarm inspection for 2019
Completed Annual extinguisher inspection for 2019
Annual Alarm Inspection
Inspected 33 Extinguishers out of 144 Annual Extinguisher Inspection
Completed Annual extinguisher inspection for 2018
Re-checked Smoke Alarms, Replaced Living Room Smoke and Replaced 6-Batteries all provided by customer ***All Normal and Reset ***
Completed Annual Smoke Alarm and Extinguisher inspections for 2018
Completed Annual extinguisher and Fire Alarm inspections for 2018
Replaced basement smoke alarm