11/7/22 confirmed with James for Thursday 11/10/22 Richard head of Security will put the Alarms in Test. SM 10/25/22 Confirmed with Hillary for Thursday 10/27/22 Richard head of Security will put the Alarms in Test. SM Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection /Mall Security needs 24 hour notice for alarms. Mall Security: 419-708-3022 Deficiency for Ansul R-102 10.5G built in: Siphon tube in far left 3 gallon tank needs to be replace. Weld is broken.
3/2 Called Asst. mgr, Terry Friess to remind of 8:00 AM appt. Texted Chris too. km 1/25 LM and texted Chris to reschedule this appt. km 1/6 Emailed Team, approved by Andrea. Confirmed with Chris, he'll have Terry there at 8:00 AM for you. Chris cell:419-260-6296 km Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Semi annual inspection of the kitchen system Annual inspection of the fire extinguishers Annual inspection of the e/lights 90 minute load test Inoperable Deficiency: Right side hood exhaust fan not working prior to test. Deficiency: Pyro Chem system has Kitchen Knight 1 & Kitchen Knight 2 tanks on same system. Deficiency: PCL-300 tank out of hydro date. Deficiency: Pressure Fryer unprotected. Deficiency: Number of Systems failed : 1 Deficiency: Number of Extinguishers Left at Job: 1 Deficiency: K-Class fire extinguisher out of hydro date. Inoperable Deficiency: Exit/Emergency combo light above front entrance has dead battery.