3/2 Called Asst. mgr, Terry Friess to remind of 8:00 AM appt. Texted Chris too. km 1/25 LM and texted Chris to reschedule this appt. km 1/6 Emailed Team, approved by Andrea. Confirmed with Chris, he'll have Terry there at 8:00 AM for you. Chris cell:419-260-6296 km Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Semi annual inspection of the kitchen system Annual inspection of the fire extinguishers Annual inspection of the e/lights 90 minute load test Inoperable Deficiency: Right side hood exhaust fan not working prior to test. Deficiency: Pyro Chem system has Kitchen Knight 1 & Kitchen Knight 2 tanks on same system. Deficiency: PCL-300 tank out of hydro date. Deficiency: Pressure Fryer unprotected. Deficiency: Number of Systems failed : 1 Deficiency: Number of Extinguishers Left at Job: 1 Deficiency: K-Class fire extinguisher out of hydro date. Inoperable Deficiency: Exit/Emergency combo light above front entrance has dead battery.
10/23 Confirmed with John, Mgr. His manager Hillary willl be on site. km Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Annual Fire Extinguisher Inspection
Responded to emergency service call Riser 2 has had several false alarms on water flow when I arrived made contact with Eric, located facp, called local fire department, and called and had system put on test, located Riser 2, checked flow switch trip times. trip times were set at 10 seconds, adjusted trip times to a minute and 15 seconds, water fluctuation varies between 155 PSI and 175 PSI pretty consistently, flow switch does not seem to be tripping prematurely anymore. tested trip time 5 different times. reset FACP ALL NORMAL. contacted local fire to let them know troublshooting complete. located fire extinguishers in Eddie's maintenance shop see attachments for pictures of fire extinguishers
Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection
Sprinkler Emergency Service Call
Alarm Systems Service Call
Emergency / Exit Lights and Portable Extinguishers Inspection