1/18 Confirmed with Samantha, manager. She'll have someone on site at 8:00 AM for us. km Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Semi-annual inspection of the kitchen system Annual inspection of the fire extinguishers Annual inspection of the e/lights 90 minute load test Deficiency: Electric connections are made inside of automan. Inoperable Deficiency: Improper system configuration. Regulated actuator is ran off low pressure side of regulated release. Also expellant hose was used. Deficiency: Number of Systems failed : 1 Deficiency: K-Class fire extinguisher is out of hydro date. Deficiency: Number of Extinguishers Left at Job: 1 Deficiency: 8- 6v-5a exit/emergency light batteries need replacing. 1- Emergency light has bad charging board needs replacement.