Very helpful, informative and took the time to explain each inspection.
9/14 - Mitch called in for service 519-410-7710 . Please do not miss. FM issue 6/24 LM for Emad km 4/23 @ 4:12 called to schedule NW 3/19-Called Emad to schedule NW Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Suppression System Inspection Annual Fire Extinguisher Inspection
NOTICE OF NON-COMPLIANCE AND REPAIR NEEDED Thank you for giving Fire Systems of Michigan the opportunity to service your fire protection needs. This proposal is being presented based on a recent inspection of your Emergency/Exit Lights and is priced to be done during normal business hours. To discuss this proposal, please contact: Rob Harrison Phone: (616) 588-0746 Email: firstname.lastname@example.org CUSTOMER AGREES TO PAY COMPANY THE FEES OUTLINED BELOW PLUS VEHICLE/FUEL CHARGES THAT MAY BE ASSESSED FOR THE CONTRACTED-FOR EQUIPMENT REPAIR OR REPLACEMENT.Sales tax is included in this quote. If your company is tax exempt, please provide tax exempt or resale certificate, otherwise sales tax will be assessed and must be paid. TERMS: NET 30 DAYS AND THIS QUOTE IS GOOD FOR SIXTY (60) DAYS FROM THE DATE OF ISSUE. COMPANY RESERVES THE RIGHT TO REASONABLY INCREASE THE FEES AND CHARGES AT ANY TIME THEREAFTER. BY SIGNING BELOW OR ELECTRONICALLY APPROVING (VIA APPROVAL/ACCEPTANCE OF THIS QUOTE ONLIN
e/lights are a load test inspection Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection Inoperable Deficiency: System is manual release only. Inoperable Deficiency: 1/4 in. expellant pipe is to great of distance to actuate third tank. Recommend having electrician move electrical box and camera so we can relocate our tank to the proper location. Inoperable Deficiency: Detection line is frayed by fifth link holder. Semi-Annual Kitchen Suppression System Inspection Annual Fire Extinguisher Inspection Annual Emergency/Exit Light Inspection
8/3 Confirmed with Chris, manager to replace tag that fire inspector ripped off. Kitchen Suppression Service Call Replace tag from Semiannual service that was done in April. Fire Inspector came in and told him he was out of date and ripped the tag off.
6/24 Approved by Brent, mgr. He'll be on site, no cooking at 8:00 and he'll manager alarms km 3/13-John confirmed the kitchen suppression inspection/aware of alarms NW Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Ansul R102-T9 (10)links (16)nozzles Annual Fire Extinguisher Inspection
Ansul R 102 9 Gallon: Semiannual Inspection of Ansul 9 gallons system Kitchen Suppression Inspection 3/12-Thomas confirmed the kitchen suppression inspection/aware of alarms NW
3/12-Krista confirmed the semi-annual kitchen suppression inspection/aware of alarms NW Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Deficiency for R-102 6G chase: No electric non fuel source shut down on filet fryer and grill system. Deficiency for R-102 6G chase: Surface protection piping from plenum supply line is galvanized pipe. Fittings from that point are also galvanized. Pipe coming from plenum to surface are welded in the hood.
Alarm Systems Inspection