Marlon and Garret did a great job, they got the job done in less time than expected, system back to normal
during previous two visits I specifically asked if any gaskets should be replaced. The serviceman that was here yesterday was very knowledgeable, but was here for four hours on overtime. not happy having to pay $1000 for a problem that wasn't fixed only diagnosed, and is now going to cost multiple thousands to fix.
Technicians left dirty finger prints on painted sprinkler pipe, left puddle of water in sprinkler room, did not call before showing up, did not walk me through work performed.
Annual Fire Alarm, Sprinkler, Backflow Inspection
Annual Backflow Inspection
Annual Sprinkler, (5) Year IPE, FDC and (3) Year Full Trip Inspection Confirmed with Ed Draper Wet Spk-1: Annual Sprinkler Inspection - Dry Spk-2: Annual Sprinkler Inspection - (5) Year Inspection - (1) FDC Backflush ($750 if CV Is On System) or ($1250 If In Vault) (2) IPE $800 (3) $25 Ea. (3) Year Full Trip On Dry Systems $800.00 Deficiency for Wet Spk-1: Dry side walls over ten your old, at both entrances 4 in total, need replaced. Deficiency for Wet Spk-1: 4 dry sidewalls over 10 years old(2003) 2 at each entrance TFP QR 155 degree model TY 3335 Sprinkler Inspection