Called on Tuesday night for non emergency service and a team was here Wednesday morning 8am!
Thank you. For your business
Jesse was efficient and did a great job with a valve wiring repair.
marc did a great job and the job was done on time with all testing completed.
Andy did a great job and was detailed and efficent
did a great job as ever
Annual Sprinkler Inspection Follow CFP Instructions SPK-1 / New Customer: Annual Sprinkler Inspection
3 troubles on AES 2 troubles on panel Upon arrival Used one 12v 8ah battery from truck stock for aes radio Cleared duct detector trouble 1 fault in AES 1 fault in panel upon departure The last trouble on panel is a mapping / programming issue we need a EST tech to reprogram. See pictures for mapping trouble
FA-2 / MR2612 @ Providence Hospital: Annual Fire Alarm Inspection EXIT-2 / MR2612 @ Providence Hospital: Annual Emergency Exit Light Inspection 2: Annual FEX Inspection Annual Fire Alarm, Fire Extinguisher, & Emergency Lights Inspection
Deficiency Repairs Fire Protection and Backflow Repair Dry SPK-2 North end of basement/Attic: FDC caps are missing. Need FDC flush. Check is at the riser. FEBCO 805YB 019562 BFP-1 1st Floor Fire Sprinkler Room: Backflow failed testing. #2 check valve assembly leaked - Recommend replacement of #2 check valve assembly. 3/4" Febco 805YB Serial #019562 Located in 1st Floor fire sprinkler riser room.
Backflow Replacement AMES 2000B 26260 BFP-2 Vault SW of property - 18' E of RR Tracks. Replacement of fire by-pass backflow.