I have been working with North West Fire since 2008 and they are always professional, do good work and with no issues and no drama.
Team knowledgeable and provides detailed information.
Deficiency Repairs Dry SPK-2 / Pump Room by Loading Dock: Dry sprinkler system is due for 3 year full trip. Pentair 4-481-11A FP-1 / In Pump Room by Loading Dock: (3) missing caps on 2.5” hose valves for fire pump test header. Recommend replacing with plastic caps as brass caps are at risk for theft. Dry SPK-2 / Pump Room by Loading Dock: Return trip to drain all low point drains following full trip of dry sprinkler system.
5 Year Inspection
Annual Fire Alarm, Sprinkler, Fire Pump, Backflow, and Fire Extinguisher Inspection; Semi-Annual Hood Inspections
Annual Fire Alarm, Sprinkler and Backflow Inspection