Helpful and friendly service!
Deficiency Repairs Watts 957 NH2280 BFP-2 3rd Floor Mech Room: Backflow failed testing. Relief did not open at 2.0 psid - Recommend full rebuild kit. 3" Watts 957 Serial #NH2280 Located in 3rd Floor mechanical room. Wilkins 375 L82483 BFP-3 Behind building in Hot box: Backflow failed testing. Relief did not open at 2.0 psid - Recommend full rebuild kit. 3" Watts 375 Serial #L82483 Located behind building in hot box.
Annual Fire Alarm, Sprinkler, Standpipe, Winterization, Backflow, and Fire Extinguisher Inspection
Quarterly Sprinkler Inspection
Quarterly Sprinkler; Semi-Annual Hood Inspection - SEE COMMENTS
Smoke detector sensitivity testing
Fire Alarm Service Call
Fire Extinguisher Service