Had repairs done recently. Staff was quick and friendly! Highly recommend!
Thomas Murphy did excellent job explaining to about the repairs he performed. He was very professional and kind to our staff members. Thank you
Marlon is always professional and friendly when he comes in. He answers any questions we may have and always does a fantastic job!
Doug was nice and explained things well. it is just a shame that he wasn't able to do/complete his job because the company sent him with the incorrect part.
Found EOL smoke detector near man door entry in alarm. Pulled down smoke detector and found a lot of dust from when ceiling tile was cut. Cleaned out smoke detector and reset panel. If the same smoke detector false alarms again i suggest replacing it . System sensor 2wT-B
Deficiency Repair Watts 009QT 438840 On kitchen Wall by ice machine: Backflow failed testing. Relief valve failed - recommend full rebuild kit. 1/2" Watts 009QT Serial #438840 Located on kitchen wall by ice machine.
Annual Backflow Inspection Follow CFP Instructions 2 fire backflow in vault need two people for confined space requirements Also vault needs to be pumped out
Annual Sprinkler Inspection Follow CFP Instructions
Replaced fire pump gauges Could not trouble shoot bldg f facp was clear