1x a/c check up. Found condenser fan motor was locked up. Replaced motor and verified operation. Unit is operating at this time. System is running without filters. I highly recommend adding filters to system. Blower motor on indoor unit is not running efficiently due to dust build up, caused by lack of filters. I recommend we take blower out and clean it. Cost will be 150$.