Great job of explaining everything, making recommendations and answering all of my questions.
Was very pleased with tech. Attitude, knowledge, professionalism.
Complaint water leaking . Cleaned trap and flushed line need filter asap 15 x20 x 1
PCSA 2021 Heating Check Up Renewal. Completed fall ck
Complaint unit freezing up. Found unit low on gas, found leaky aluminum lineset. Lineset needs to be replaced so unit can hold refrigerant for more than a month. Further attention is necessary
Water dripping, filled drain, found crack in drain pan. Need to replace drain pan, shut off system, itâ€™s pouring water Ordered new pan, will schedule repairs when it comes in. 70 degrees in hallway with unit off. Siliconed the crack to try to get them by temporarily 9/9 returned and replaced drain pan, performed fall 2021 maintenance Thermostat on south Sanctuary system was shorting out and needed replaced. Capacitor on blower motor for fellowship Hall was getting very weak and needed replaced. Capacitor on outdoor coil for south Sanctuary system was getting weak and needed replaced. Condensate pump for south system may need T installed to help prevent system from leaking in attic. Freeze sensor on evaporator coil for south system needs to be replaced as soon as possible. Everything else was clean and checked out well. All systems are operating normally at this time. Replaced freeze stat.
Start PCSA a/c maintenance Took pics of capacitors replaced for Derek, I let his wife know that Iâ€™m hoping the charge adjustment solved his water problem, the coil is not accessible so I couldnt dig into it much deeper. The drain isnâ€™t clogged and I did flush it. I think the fitting that sits at the base of the coil may be uninsulated and is causing condensation. Added 1 lb of gas and siliconed under that door. Did the best I could on this.
Complaint P.D. not cooling Blower ordered will be here tomorrow 8/31 returned and replaced blower motor and capacitor, system is cooling
Ameren pinpointed gas leak in fitting in furnace
Quote for new system
Need leak search send Steve all micro channel
Installed 17 SEER York 2 1/2 ton heat pump on new construction
Replaced 2 sets of busted condensate drains in attic. Flushed with water to check new joints.
PCSA 2021 PREPAID AC MAINTENANCE Condenser fan motor needs to be replaced very soon. Everything else was clean and checked out well.
PCSA 2021 PREPAID AC MAINTENANCE Filter changed Blow grass away from unit
PCSA 2021 PREPAID AC MAINTENANCE All checks good Drain flushed Filters changed