Was very pleased with tech. Attitude, knowledge, professionalism.
No cooling, added 1 lb 410a, system is a microchannel coil inside and out, recommend leak search
Water on ceiling, cut out burst piece of copper, sweat in a new sleeve. Tested and itâ€™s not leaking
Complaint not cooling, found bad outdoor capacitor, replaced, cycled cooling, checked charge, added 1 lb r410a, replaced filter system is cooling
2021 PCSA a/c cooling maintenance prepaid Outdoor capacitor needed replaced. (Warranty) Everything else was clean and checked out well. System operating normally.
2021 PCSA prepaid a/c maintenance washed unit ckd system unit has R-22 ref.
Double stack not closing all stacks. Replaced. Heaters both on now
Unit is frosting up Frost on unit, changed defrost curve to setting 2 per manual. Defrost ran great
Need a 6 inch 4x 10 boot for replacement Wednesday 330
Complaint: Heat Pump Frozen up Found board switching to defrost but not putting out signal for reversing valve to slide. Replaced board, cycled defrost 4 times, knocked as much ice off unit as I could, system is heating
Cause of the issue was bad thermostat batteries. Replaced batteries and system is operating normally at this time.
Inspected flex runs under house. Found several to be laying on the ground and the one going to the kitchen completely detached. Resecured all runs ants replaced the one going to the kitchen. Wasnâ€™t able to find any other signs of damage to flex runs. Cleaned return grill on closet door. Wasnâ€™t allowing much if any air flow. Everything appears to be operating normally at this time.
NO heat, cleaned flame sensor, vacuumed furnace, cleaned burner crossovers system is heating
RENEWAL 2020 PCSA Filter changed by customer all checks good. System has 2 contactor s be sure to inspect in future
2020 PCSA Renewal Need to monitor defrost operation, unit was iced up upon arrival but defrosted normally. Charge is on the money. Replaced dual cap